21:40 May 4, 2020
En Revision Imported Date 5/11/2020
EN Revision Text: DIESEL GENERATOR COOLING WATER SYSTEM DECLARED INOPERABLE
This report is being made pursuant to 10 CFR 50.72(b)(3)(v)(D), Event or Condition that could have prevented fulfillment of a Safety Function needed to mitigate the Consequences of an Accident. A through wall leak was found on piping connected to the Division 3 Diesel Generator (DG) Cooling Water Strainer. This condition has been evaluated and the Division 3 DG Cooling Water System has been declared inoperable. The Division 3 DG Cooling Water System is a support system for the Division 3 Emergency DG and the High Pressure Core Spray System (HPCS).
The NRC Resident Inspector has been notified.
This update retracts Event Notification #54693, which reported a condition that could have potentially prevented fulfillment of a safety function needed to mitigate the consequences of an accident.
An evaluation of the flaw on the piping connected to the Unit 2 Division 3 Diesel Generator (DG) Cooling Water strainer concluded that the system would have remained operable. The High Pressure Core Spray system, supported by the operable DG Cooling Water system, remained operable and capable of performing its safety function.
The NRC Resident Inspector has been notified.Notified R3DO (Stone).
Illinois (NRC Region 3)
|10 CFR 50.72(b)(3)(v)(D), Loss of Safety Function - Mitigate the Consequences of an Accident|
|LER:||look for an ler...|
|Time - Person (Reporting Time:+2 h0.0833 days <br />0.0119 weeks <br />0.00274 months <br />)|
23:40 May 4, 2020
|NRC Officer:||Donald Norwood|
|Last Updated:||May 8, 2020|
|54693 - NRC Website|