|ENS 53999||14 April 2019 06:44:00||At 0320 EDT, April 14, 2019, Sequoyah Unit 1 experienced an automatic reactor trip. The event was initiated by the trip of the 1A main feedwater pump. During the automatic unit runback, an automatic reactor trip was initiated due to low-low level in Steam Generator number 3.
The Auxiliary Feedwater System (AFWS) automatically actuated as required when the expected post-trip feedwater isolation actuated. Reactor Coolant System temperature is being maintained by the AFWS and the steam dump system. During this operational cycle, one control Rod Position Indicator (RPI) for core position E-5 in shutdown bank 'A' has been inoperable, and the appropriate Condition and Required Actions of (Technical Specification Limiting Condition of Operation) 3.1.7 were complied with. Due to this inoperable RPI, the associated shutdown rod is conservatively assumed to be full out and untrippable. Consequently, boration was required to establish adequate shutdown margin. All other Control and Shutdown rods fully inserted. All safety systems responded as designed. No primary or secondary safety valves actuated during or after the reactor trip. The unit is currently stable in Mode 3. Unit 1 is in a normal shutdown electrical alignment.
There was no impact on Unit 2.
Due to the Reactor Protection System actuation while critical, this event is being reported as a four-hour, non-emergency notification per 10 CFR 50.72(b)(2)(iv)(B) and in accordance with 10 CFR 50.72(b)(3)(iv)(A) as an event that results in a valid actuation of the AFW system.
There was no impact on the health and safety of the public or plant personnel.
The NRC Senior Resident Inspector has been notified."|