Welcome to www.kanterella.com Wiki site! The goal of this site is to apply semantic elements to Nuclear information.
If you would like to discuss this site or if you have cool ideas please visit the Community page.
An Adams import was set up so that new correspondence will be imported periodically. If we can add context then we could better organize the letters into relevant groups. Ie groups around project codes.
Plants undergo inspections by the NRC. A series of pages have been uploaded representing the findings that resulted from those inspections. This is a good data set because it helps show a practical interpretation of regulation. In other words, who knows what it really means but this is how it was done wrong.
One of the bigger events for a plant is a Scram. The occurrence of which are reported to the NRC via the ENS system. By extracting that information you can get lists of data. Please see the main page Scram.
Recently Mapping has been incorporated to the wiki. Mostly its about plant locations and can show corporate owner icons. It is feasible to overlay a set of data with locations (ie you can see where ENS occurred on a Map).
First successfully integrated database is the Emergency Notification System. It is a database which holds all the short-term notifications made by nuclear power plants (10 CFR 50.72). If you visit the Emergency Notification System you can see how digitizing the ENS can lead to a variety of customized reports and notifications.
Since Yesterday: 05-19-2019
|ENS 54073||Arkansas Nuclear||Safety Parameter Display System||On May 19, 2019, at 1809 CDT, the Safety Parameter Display System (SPDS) was lost to both Arkansas Nuclear One Units 1 and 2 due to the SPDS Inverter (2Y-26) failure. The SPDS Inverter is the power supply to both units' SPDS. The Unit 2 Control Room dispatched operators in response to a smoke alarm received from the 2Y-26 Inverter room. Upon arrival, smoke was reported emanating from 2Y-26. There was no report of fire at any time. Field operators de-energized 2Y-26 and the smoke ceased. The loss of SPDS also caused the Power Operating Limits (POL) function of the Unit 2 Core Operating Limits Supervisory System (COLSS) to be lost, so Unit 2 reduced power to 91 (percent) in accordance with Technical Specifications. Both units are at power and stable.
The NRC Resident has been notified.This is reportable per 10 CFR 50.72(b)(3)(xiii)."