|Entered date||Event description|
|ENS 54687||1 May 2020 11:53:00|
At 1000 EDT on May 1 2020, Operations commenced a shutdown of DC Cook Unit 2 to comply with LCO 3.4.13, Condition B Reactor Coolant System (RCS) pressure boundary leakage. At 0354 EDT on May 1, 2020, Operations detected an estimated 8 gpm Reactor Coolant System leak. The source of the leak could not be identified and Tech Spec 3.4.13, Condition A was entered for unidentified RCS leakage in excess of the 0.8 gpm limit. At 0745 EDT on May 1, 2020, Unit 2 entered LCO 3.4.13, Condition B when the 4-hour limit to complete the required actions of Condition A could not be met. At 0945 EDT on May 1, 2020, Unit 2 entered LCO 3.4.13, Condition B when the 4-hour limit to complete the required actions of Condition A could not be met. At 0945 EDT on May 1, 2020, inspections inside containment identified the leak as pressure boundary leakage from a pressurizer spray line which also requires entry into LCO 3.4.13, Condition B. At 1059 EDT on May 1, Unit 2 was tripped from 15 percent power. All systems functioned normally. This event is reportable under 10 CFR 50.72(b)(2)(i), the initiation of any nuclear plant shutdown required by the plant's Technical Specifications as a 4-hour report and under 10 CFR 50.72 (b)(3)(ii)(A), degraded condition, as an 8-hour report. The NRC Resident Inspector has been notified.
The condition identified in EN #54687, pursuant to 10 CFR 50.72 (b)(3)(ii)(a) has been evaluated, and has been determined not to be RCS pressure boundary leakage. As such, the 8-hour report is being retracted, as it is not an event or condition that results in, 'the condition of the nuclear power plant, including its principal safety barriers, being seriously degraded.' The leakage was subsequently determined to be from the tell-tale nipple of a pressurizer spray valve, not from the pressurizer spray line piping as previously reported. The Reactor Coolant Pressure Boundary (RCPB) is formed by the valve body, plug, seat, body to bonnet extension, and bonnet of the pressurizer spray valve. Therefore, the leakage is not RCPB leakage. There is no change to the 4-hour report made under 10 CFR 50.72(b)(2)(i), the initiation of any nuclear plant shutdown required by the plant's Technical Specifications. The NRC Resident Inspector was notified of this retraction. Notified R3DO (Stone).