From kanterellaJump to navigation Jump to search
The following violation of very low safety significance (Green) was identified by the licensee and is a violation of NRC requirements which met the criteria of the NRC Enforcement Policy, for being dispositioned as a NCV. Unit 1 and Unit 2 facility operating license DPR-71 and DPR-62 condition 2.B.(6)requires, in part, that the licensee shall implement and maintain in effect all provisions of the approved fire protection program. Procedure AD-EG-ALL-1522, Duties of a Fire Watch, requires periodic fire watches to be performed within their designated time periods including any allowed grace periods. Contrary to the above, during the spring 2017 Unit 2 refueling outage, between March 1 and March 19, selected periodic fire watches were missed or not performed within the required grace periods. The finding was screened using IMC 0609, Appendix F Fire Protection Significance Determination Process, and was determined to be of very low safety significance (Green), because the reactor was able to reach and maintain safe shutdown. This issue was documented in the licensees CAP as NCR 2115035.
|Report||IR 05000324/2017004 Section 4OA7|
|Date counted||Dec 31, 2017 (2017Q4)|
|Inspectors (proximate)||G Smith|
Finding List (Brunswick) @ 2017Q4
Self-Identified List (Brunswick)