NRC-98-0040, Application for Amend to License NPF-43,requesting to Allow one-time Extension of Surveillance Intervals to Delay Shutdown for Upcoming Sixth Refueling Outage (RFO6) Until 980904
B17350, Responds to NRC Re Violations Noted in Insp Repts 50-245/98-207,50-336/98-207 & 50-423/98-207,respectively. Corrective Actions:Issues Were Discussed W/Personnel Directly Involved in Preparation of Licensing Submittal
A09920, Discusses Review of R1-91-A-0219 Re Various Activities at Millstone Unit 2.W/related Matl
05000364/LER-1998-004-01, :on 980420,failure to Perform Penetration Room Filtration Sys SR Was Noted.Caused by Personnel Error.Note Has Been Corrected & Initial Review of Surveillance Schedules Have Been Performed
05000498/LER-1987-009, :on 870918,determined That Atmosphere Monitor Surveillance Test Did Not Include Monitor Iodine Channel. Caused by Procedural Inadequacy.Procedure Revised & Reviewed
05000352/LER-1987-030, :on 870604 & 05,failure to Perform Monthly Functional Tests of Channels D & B of Refueling Area Ventilation Exhaust Radiation Monitors Discovered.Caused by Personnel Error.Surveillance Tests Performed
05000461/LER-1992-007-01, :on 920623,determined That Previously Performed Testing for Loss of Power Not in Accordance W/Ts.Caused by Misinterpretation of Test Requirements by Writers. Procedures Will Be Revised Per TS
05000354/LER-1995-018-01, :on 950720,surveillance Test Was Missed Due to Procedure & Personnel Error & Automatic Depressurization & HPCI Sys Inoperability.Memo Sent to All I&C Supervisors & Technicians Re Event
05000413/LER-1990-006-04, :on 900711,determined That Instrumentation & Electrical EMF-43B High Radiation Setpoint Above Tech Spec Setpoint Value.Caused by Inappropriate Action.Review Conducted of How Setpoint Changes Controlled
05000324/LER-1980-116-03, /03L-0:on 801231,pressure Switch 2-E11-PS-N010A Actuated Outside Tech Spec Limits.Caused by Instrument Drift.Switch Recalibr
05000272/LER-1996-041, :on 961228,surveillance for Radiation Monitors Source Check Required by TS Was Missed.Caused by Lack of Attention to Detail.Reemphasized Mgt Expectations Concerning Surveillance Test Accountability
HNP-99-149, Application for Amend to License NPF-63,implementing Selected Improvements Described in GL 93-05
05000400/LER-1996-010-02, :on 960628,identified Surveillance Testing Deficiencies That Caused Past Entries Into TS 3.0.3.Caused by Personnel Error.Surveillance Test Procedures OST-1008 & OST-1092 Revised
05000400/LER-1996-010, :on 960628,surveillance Test Deficiencies Identified in Quarterly RHR Sys.Caused by Inadequate Test Procedures Resulting from Personnel Errors.Scheduled Tests on Administrative Hold & Procedures Revised
05000315/LER-1999-015, :on 990408,RM Sys Was Not Tested IAW TS Srs. Caused by Inadequate Implementation of TS SRs in Plant Surveillance Procedures.Channel Functional Testing of RM Sys Unit Vent Effluent RMs Was Successfully Completed
05000389/LER-1990-003-03, :900726,determined That Main Steam Line Radiation Monitor Returned to Svc Following Power Supply Replacement W/O Performing Required Tech Spec Surveillance. Caused by Personnel Error.Personnel Counseled
05000369/LER-1989-031, :on 891012,ac Power Supply Fuse Blew Resulting in Automatic Isolation of Four Outside Air Intakes on Ventilation Sys.Caused by Inappropriate Action.Intake Valves Returned to Svc & Tech Spec 3.3.3.1 Exited
05000348/LER-1981-008-03, /03L-0:on 810313,surveillance Tests for Tech Spec 4.3.3.1 for Radiation Monitors R25 a & B Not Performed within Required Period.Caused by Personnel Not Properly Assessing Conditions for Surveillance.Test Schedule Revised
05000530/LER-1996-001-02, :on 960621,inaccurate Gas Calculations for Post Accident Sampling Sys Occurred.Caused by Surveillance Test Worksheet Errors.Independent Investigation of Event Being Conducted