RA-17-072, License Amendment Request - Proposed Defueled Technical Specifications and Revised License Conditions for Permanently Defueled Condition
RA-08-009, Draft - Outlines (Folder 2) (Facility Ltr. Dtd. - 01/16/08), Submittal of Initial Operator Licensing Examination Outline
B11689, Application for Amend to License DPR-21,revising Tech Specs to Define Refuel Condition & Operability Requirements of Sys During Refuel & Shutdown Conditions.Fee Paid
05000333/LER-1989-006-01, :on 890419,standby Liquid Control Sys Declared Inoperable When Pump Discharge Accumulator Nitrogen Precharge Was 0 Psig.Caused by Slow Leak in Charging Connector Spring Loaded Valve.Bladder Repaired
05000293/LER-1998-019, :on 980727,declared Standby Liquid Control Subsystem B Inoperable.Caused by Leakage Through Pipe Fitting on Pressure Gauge PI-1160B.Removed Subject Gauge, Cleaned Pipe Threads & Reinstalled Gauge
05000281/LER-1986-011-02, :on 860720,determined That Svc Water Leaking Into Containment from Recirculation Spray HX (Rshx).Caused by Leaking Tubes in RSHX B.Tubes Plugged.Rshx Successfully Pressure Tested
05000281/LER-1986-006-03, :on 860616,svc Water Leak Discovered in Expansion Joint on Svc Water Return Line from Recirculation Spray Hx.Caused by Galvonic Corrosion.Expansion Joints Replaced & Carbon Steel on Joints Coated
05000247/LER-1983-040-03, /03L-0:on 831026,during Plant Starup Following Maint Outage,Vol of Water in Condensate Storage Tank Reduced Below Tech Specs.Caused by Effort to Maintain Concentrations of Sodium Chloride within Limit
05000247/LER-1983-025-03, Flow Control Valve 406A on Auxiliary Feedwater Pump 21 Discharge Line to Steam Generator 21 Did Not Open During Surveillance Test.Caused by Chipped Valve Cage.Cage & Gaskets Replaced
05000247/LER-1983-005-03, /03L-0:on 830308,while Bringing Auxiliary Feedwater Pump Up to Operating Speed for Bimonthly Surveillance Testing,Outboard Bearing Started to Smoke. Caused by Pump Bearing Needing Repacking.Pump Repacked
05000247/LER-1982-050-03, /03L-0:on 821231,during Startup Following Cycle 5/ 6 Refueling Outage,Amount of Water in Condensate Storage Tank Reduced Below Tech Specs.Caused by Efforts to Minimize Chloride Concentration Into Steam Generators
05000219/LER-1982-050-03, /03L-0:on 820828,reactor Vessel Pressurized in Excess of 110 Psig W/Reactor Water Temp Greater than 212 F. Caused by Inadequate Procedure 602.4.001.Test Procedure Will Be Reviewed to Redefine Temp/Pressure Requirements
05000219/LER-1982-006, Forwards LER 82-006/01T-0.Detailed Event Analysis Encl
05000219/LER-2009-004, Regarding Establishment of Secondary Containment Boundary Contrary to Technical Specification Requirements
05000306/LER-1997-003-01, :on 970517,Unit 2 Was Brought to Planned Hot Shutdown Condition to Perform Valve Maint in 22 RCP Containment Vault.Caused by Inattention to Detail.Will Evaluate Revising Plant Operating Procedures
BECO-LTR-96-040, Application for Amend to License DPR-35,proposing Part of Overall Effort to Improve Outage Performance at Plant
05000219/LER-1998-003-01, :on 980303,failure to Perform High Drywell Pressure Check Surveillance Was Noted.Caused by Inadequate Procedure.Reviewed & Revised Appropriate Plant Documents & Provided Operator Training