Sheldon Clark# QUERYbbee27a629086a836a7e499291d346f1
Sheldon Clark# QUERY1548183e19cee6305293618dfc3836cc
Sheldon Clark# QUERY2ea3e6eda6b7776254585657e5c931bf
Sheldon Clark OR Sheldon Clark
Sheldon Clark# QUERY2ee934a3dc29d8bba5edefb97f8f4ff7
Sheldon Clark# QUERY1b5fa4f1d44d397c436c1536f1457a83
Sheldon Clark# QUERY219b4ebc89e4154c17a9d154a51366ca
Sheldon Clark
Sheldon Clark# QUERYd206a8f0e38bad8e35334f2f88194553
Sheldon Clark# QUERY39e85b17afb5bb555ea6870489e99526
NRC/OGC/GCRPS/RMR false
Sheldon Clark# QUERYdc95e0d02aa071559e636fd1d942f99f
NRC/OGC/GCRPS/RMR true
Sheldon Clark# QUERY7f91ecf1227e4165566c0be24a0c89dd
Sheldon Clark# QUERY3b7824ddb99ef0779b9e4ca6b905773d
CNS-15-074, CISI-1462.10.0040, Revision 0, Fourth Interval Inservice Inspection Outage Schedule, Quality Assurance Program Related
05000295/LER-1979-096-03, /03L-0:on 791120,low-low Tave Comparator 1TC432GD Outputs Found Low,Exceeding Tech Specs Limit.Caused by Instrument Drift of Unknown Origin.Comparator Tested, Recalibr & Returned to Svc
05000304/LER-1980-024-99, /99X-0:on 800723,while Putting Safeguards Back in Svc,Safety Injection Was Actuated from Train B Only.Caused by Procedural Change Which Confused Operator.Procedure Clarified
05000295/LER-1980-037-03, /03L-0:on 800812,during Normal Operation While Performing Monthly Functional Tests of 63AST Reactor Trip Switches,Switches Were Set 11 Psig Off in Nonconservative Direction.Caused by Faulty Test Gauge
05000295/LER-1980-024-03, /03L-0:on 800515,while Performing PT-10,safeguards Actuation tests,1A Svc Pump Failed to Start from Train a of Safeguards.Caused by Contacts for Safeguards Actuation Making Intermittent Contact.Contacts Adjusted
05000295/LER-1980-012-03, /03L-0:on 800312,during Normal Power w/1B Diesel Generator in Standby,Dc Control Breaker Tripped.Caused by Use of 5-amp Slow Blow Fuses in Annunciator Inverter.Slow Blow Fuses Replaced W/Fast Blowing Fuses
05000295/LER-1979-078-01, /01T-0:on 791018,four Pipe Penetration Solenoid Valves Not Qualified on Each Unit.Caused by Use of Nonqualified Solenoids.Solenoids Will Be Replaced
05000304/LER-1979-038-03, /03L-0:on 790718,while Performing Periodic Testing,Recirculation Sump to RHR Pump Suction Valve Failed to Stroke Open.Caused by Failure of stem-mounted Limit Switch Interlock Contact on Valve 2MOV-RH8700A to Make Up
05000295/LER-1979-056-01, /01T-0:on 790801,noted That Reactor Coolant Isolation Valves Have D2400X Limit Switches in Train B Reactor Protection Circuits.Switches Unsuitable for post-LOCA Environ & Will Be Replaced During Next Outage