Scott Freeman# QUERY89c73a7e637d3b69e2e66635e2c712e0
Scott Freeman# QUERYdf774e4f754924d05036c8b2cfaa4b70
Scott Freeman OR Scott Freeman
Scott Freeman# QUERY75ae66d704e19b60adb2aa98206541ef
Scott Freeman# QUERY9482b928f20d6eb1f712e6c102caeb01
Scott Freeman# QUERY45b31ec78070eb227a8c04369165c096
Scott Freeman
Scott Freeman# QUERY979b2e803cdc52bcc545c77cf12fc69a
Scott Freeman# QUERYd735a282b20f7b1ac3338ed867bd271b
Reactor Projects Region 2 Branch 6 false
Scott Freeman# QUERY834694331c6147496d04ae341bf0cad5
Reactor Projects Region 2 Branch 6 true
NRC Region 2
Scott Freeman# QUERY2ce199292f8f348c2d3f87c930a7b427
Information Notice 2002-07, Use of Sodium Hypochlorite for Cleaning Diesel Fuel Oil Supply Tanks
05000416/LER-1982-180, Final LER 82-180/03L-0:on 821227,isolation Valve for Hose Station in Control Room Replaced Due to Leaking Which Pressurized Hose.Addl Hose Run to Supply Backup Fire Protection.Leaking Valve Replaced.Sys Returned to Svc
05000416/LER-1982-182-03, /03L-0:on 821229 & 31,two Fire Doors Blocked Open to Perform Maint.Open Fire Doors Contrary to Tech Spec 3.7.7.Limiting Condition of Operation & Fire Watches Established.Maint Completed & Doors Closed on 830103
05000416/LER-1982-112-03, /03L-0:on 821105,smoke Detector in East Switchgear & Piping Penetration Rooms of Auxiliary Bldg,Elevation 119 Ft,Alarmed & Would Not Reset.Caused by Dust in Detector. Detector Cleaned & Returned to Svc on 821108
05000416/LER-1983-018-99, /99X-0:on 830105,diesel Generator 11 Unloaded & Secured Following Trip on High Bearing Temp & Indication of Increased Crankcase Pressure.Caused by Loose Sensor on Rear Main Bearing Allowing Air to Vent Off Pneumatic Logic Sy
05000416/LER-1982-183-99, /99X-0:on 821222,smoke Detection Zone Covering Auxiliary Bldg Corridor Area Alarmed & Would Not Reset.No Smoke or Fumes Present.Zone Found Functionally Operable & Alarms Reset
05000416/LER-1982-114-03, /03L-0:on 821108,smoke Detector in Zone Covering Control Bldg,Elevation 166 Ft & 177 Ft,Alarmed & Would Not Reset.Caused by Damage to Detector Due to Installation Work in Area.Detector Replaced & Tested Satisfactorily
05000416/LER-1983-014-03, /03L-0:on 830107,during Cold Shutdown,Supervisory Sys Alarms for Several Fire Doors Found in Continuous Alarm & Would Not Reset.Caused by Problems W/Limit Switches, Latches & Magnets.Fire Watch Established.Doors Reworked
05000416/LER-1983-024-03, /03L-0:on 830114,several Smoke Detector Zones in Auxiliary Bldg & Control Bldg Would Not Reset.Cause Attributed to Spurious Action.One Detector Replaced & Remaining Detectors Cleaned
05000416/LER-1983-020-03, /03L-0:on 830115,during Shutdown,Lube Oil Heater on Diesel Generator 12 Failed,Resulting in Diesel Generator 12 & Div 2 ECCS Being Declared Inoperable.Caused by Overheating & Shorting to Ground.Heater Replaced
05000416/LER-1983-019-03, /03L-0:on 830112 & 20,one Smoke Detector in Zone 1-15 & Eight Detectors in Zone 2-18 Covered During Planned Maint Functions to Prevent False Alarms or Damage to Unit. Detectors Uncovered After Maint Completed
05000416/LER-1982-163-03, /03L-0:on 821211,during Routine Power Supply Switching Operation,Both Shutdown Cooling Loops Isolated. Caused by Momentary Loss of Power to Rps.Shutdown Cooling Restored
Information Notice 2002-02, Recent Experience with Plugged Steam Generator Tubes
05000416/LER-1982-132-01, /01T-0:on 821130 & 1202,several fire-rated Electrical Penetrations Found Open.Penetration Openings Authorized by Maint Work Orders W/O Notifying Control Room. Instructions Issued to Responsible Persons