GNRO-2013/00051, Responses to NRC Requests for Additional Information Pertaining to the Final Report for the GGNS Replacement Steam Dryer
SVPLTR 04-0001, Final Third 10-Year Interval Inservice Inspection (ISI) Summary Report
05000414/LER-1986-041-01, :on 860904,safety Injection Actuated on Low Main Steam Line Pressure.Caused by Condenser Control Valve Malfunction Creating Line Depressurization.Safety Injection & Containment Isolation Signals Reset
05000482/LER-1986-044, :on 860902,partial Loss of Offsite Power Occurred.Caused by Personnel Error During Routine Substation Switchyard Maint Activity.Increase in Testing Frequency of Valve Ef HV-38 Implemented
05000361/LER-1982-167-03, /03L-0:on 821218,w/both Units in Mode 5,control Room Emergency Chiller E-336 Tripped on High Bearing Temp & Declared Inoperable.Caused by Faulty Solenoid Valve for Motor Oil Cooling Unit of Chiller.Valve Replaced
05000366/LER-1982-018-03, Evidence of Main Steam Pipe Hanger Embed Plate Pulling from Ceiling Found.Caused by Concrete Spalling Around Embed Plate Due to Localized Detective Matl &/Or Faulty Installation
05000361/LER-1982-052-03, /03L-0:on 820419,during Routine Shift Surveillance,Channel B Ammonia Analyzer of Toxic Gas Isolation Sys Was Declared Inoperable.Caused by Instrument Drift.Analyzer Repaired & Recalibr
05000366/LER-1982-028-01, /01T-0:on 820402,standby Gas Treatment Filter Train 2T46-D001B Found Out of Compliance W/Tech Spec.Caused by Error in Testing Procedure.Charcoal Replaced & Tested. Procedure Revised
05000261/LER-1981-007, Updated LER 81-007/01T-1:on 810122,potential Modeling Error in ECCS Model Used for LOCA Analysis Reported.Caused by Shift in Peak Clad Temp.New ECCS Analysis Performed in Aug 1981.No Impact on Public Health & Safety
05000298/LER-1981-018-03, /03L-0:on 810625,pressure Switch NBI-PS-52A Found W/Trip Point Less Conservative than Tech Spec.Apparently Caused by Setpoint Drift.Switch Readjusted.Setpoints for Switches Reset
05000370/LER-1989-010-04, :on 890905,leak Occurred in Auxiliary Bldg Pipe Chase,Causing Decrease in Refueling Water Storage Tank Level & Release of 10,000 Gallons of Water Through Gasket.Caused by Procedure Deficiency.Gasket Replaced
NUREG-0153, NRC Staff Response to ASLB Questions Concerning Generic Safety Issues.Conclusions in Perkins SER Re Issuance of Const Permits Will Not Be Affected by Results of Generic Tasks.W/Certificate of Svc.Supporting Documents Encl
L-2018-176, Subsequent License Renewal Application, Responses to the August 2018 NRC On-Site Regulatory Audit Follow-Up Items
L-87-461, Forwards Summary of mgt-on-shift Repts,Per NRC 871029 Order
05000295/LER-1979-082-03, /03L-0:on 791006,failed Fuel Letdown Liquid Rad Monitor 1RT-PR27 Failed Low & Could Not Be Reset.Cause Unknown.Monitor Reconnected & Returned to Svc
W3P87-2060, Forwards Changes to QA Program (FSAR Section 17.2) Re Significant Transition at Facility from Const to Operations Phase Which Included Major Reorganization of Nuclear Operations Dept.Fee Paid