GO2-82-040, Interim Deficiency Rept Re Incorrectly Specified Design Temps for Containment Penetration Piping/Valves.Supply Sys Engineering Conducting Technical Evaluation of Ae Rept.Next Rept by 820707
GO2-83-160, Final Deficiency Rept 190 Re Excessive Cable Length Causing Voltage Drop.Initially Reported on 820511.Control Power Transformer Increased from 300 VA to 500 VA to Preclude Voltage Drop
GO2-82-956, Confirms 821123 Telephone Request for Extension Until 821203 to Provide Response to IE Insp Rept 50-397/82-21
GO2-83-178, Forwards Emergency Plan Implementing Procedures,W/Exception of EPIP 13.1.1, Classification of Emergency. EPIP 13.1.1 Will Be Submitted by 830315.W/o Encl
GO2-83-241, Responds to NRC Re Violations Noted in IE Insp Rept 50-397/83-03.Corrective Actions:Task Force Team Leaders Instructed to Review Letterbooks to Assure No Unanswered Quality Concerns Exist.Ir 3674 Addressed in Overall Review
GO2-83-253, Interim Deficiency Rept Re Loss of ESF Loads on Under Voltage Trip.Initially Reported on 830228.Project Engineering Directive 218-E-4618 Issued to Implement Corrective Action.Next Rept Expected by 830624
GO2-83-254, Notifies That Util Deferring Indefinitely,Plans to Install Continuous Nitrogen Supply Sys to Containment Electrical Penetrations,In Response to IE Bulletin 77-07,based on Industry Experience
GO2-83-237, Forwards Emergency Classification Procedure PPM 13.1.1, Classifying Emergency, Per NUREG-0696.Use of Safety Parameters in symptom-based Methodology More Functional Approach than event-based Methodology
GO2-82-806, Interim Deficiency Rept Re Improper Installation of Concrete Expansion Anchors & Unacceptable Concrete & Grout Work. Initially Reported on 820403.Corrective Actions Continuing. Next Rept Will Be Submitted on 821218
GO2-82-819, Final Deficiency Rept Re 4.16 Kv Breakers DG 1-7 & DG 2-8 & Interim Deficiency Rept Re Emergency Diesel Generators DG-1 & DG-2 Airstart Circuits.Initially Reported on 820830 & 0908,respectively.Next Rept Will Be Submitted by 821220
GO2-82-380, Forwards Final Response to NRC IE Bulletin 79-02,Revision 2
GO2-82-037, Interim Deficiency Rept Re Reportable Conditions 177 Concerning Bulk Purchase Valves & 175 Wbg Radiographs.Next Rept Expected 820601.All Subsequent Repts Will Be Provided on Quarterly Basis Until Final Rept Is Filed
GO2-83-188, Final Deficiency Rept Re Damage to Electrical Cable 2SM8- 0080 During Installation of Thermo Lag Fire Resistant Matl (Condition 235).Initially Reported on 830204.Damaged Cable Repaired.Condition Not Reportable Per 10CFR50.55(e)
GO2-83-174, Final Deficiency Rept on Conditions 208,209,223 & 229 Re Remote Shutdown Panel,Rhr & LPCS Pump Discharge Pressure Switches,Standby Liquid Control Sys & Missing Hangers in Turned Over HPCS Sys 7.1,respectively.Next Rept Due 830523
GO2-83-154, Forwards Final Deficiency Repts Re Skewed T Joints & Interim Deficiency Repts Re RHR Relief Valve Vents & LPCS & RHR Support Pin Receptacles
GO2-83-295, Amends Response to NRC Re Violations Noted in IE Insp Rept 50-397/82-21.Corrective Actions:Fsar Rev & Rev 2 to Electrical Separation Practices Document Will Be Issued by 830415
GO2-82-955, Deficiency Rept Re Johnson Controls Design Issue.Eight of 132 Small Bore Lines Did Not Meet Min Design Criteria Following Thermal Effects Application
GO2-82-858, Submits Clarification to IE Bulletin 79-14, Seismic Analysis for As-Built Safety-Related Piping Sys. As-built Drawings Given Addl Piping & Support Checks by Contractor Field Engineers Rather than by Qa/Qc Inspectors
GO2-82-727, Final Deficiency Repts Re Conditions 175,WBG Radiographs & 177,bulk Purchase Valves.Initially Reported on 811119 & 1208,respectively.All Quality Class I Welds Accounted For. Wbg Documentation Review of Bulk Purchase Valves Complete
GO2-82-989, Final Deficiency Repts 210 & 218 Re Deficient Emergency Diesel Generators DG-1 & 2 Airstart Circuits & MSIV Leak Control Sys,Respectively.Initially Reported 820830 & 1111. Silver Plated Contacts to Be Replaced in Airstart Circuits
GO2-82-992, Forwards Final Rept on Onsite Review of Radiographs,Per IE Bulletin 82-01,Rev 1, Alterations of Radiographs of Welds in Piping Subassemblies. All Corrective Action Completed
GO2-82-807, Final Deficiency Rept Re High Resistance Cable Grounding of 4.16 Kv Diesel Generators.Initially Reported on 820506. Manufacturers Advised That Equipment Can Operate for Indefinite Period w/line-to-ground Fault W/O Damage
GO2-82-803, Advises That Deficiency Repts Re Electrical Cable Routing, Termination,Labeling,Power Supplies & QC Documentation Have Been Reopened.Interim Repts Will Be Provided by 821218
GO2-82-723, Responds to NRC Re Violations Noted in IE Insp Rept 50-397/82-14.Corrective Actions:Bechtel Procedures Reviewed to Ensure That Ae Approvals Obtained & QC Administrative Instruction 15 Issued
GO2-82-764, Forwards Interim Deficiency Repts 208 Re Remote Shutdown Panel & 209 Re Pump Discharge Pressure Switch
GO2-82-605, Final Deficiency Rept 179 Re Containment Penetration Piping/Valves.Initially Reported on 820218.Supply Sys Engineering Evaluation Rept Determined That Ae Properly Specified Temp for Piping & Valves
GO2-82-689, Interim Deficiency Rept Re Johnson Controls Design Issue. Initially Reported on 820720.Analysis of Large Bore Piping & Small Bore Design Underway.Next Rept Expected by 821123
GO2-82-676, Final Deficiency Rept Re Defect in 35-130-200 Battery Chargers Supplied by Power Conversion Products,Inc.Initially Reported on 820716.Replacement of 200 Ampere F1,F2 & F3 Fuses w/300 Ampere Fuses Recommended
GO2-82-574, Interim Deficiency Rept Re Concrete Expansion Anchor Program & Concrete & Grout Work.Evaluation Incomplete Due to Complexity of Interfacing Issues.Next Rept to Be Submitted by 820908
GO2-82-554, Forwards Interim Rept Per IE Bulletin 82-01,Revision 1 Re Radiographs of Welds in Piping Subassemblies.Rept Describes Findings & Corrective Actions Taken.Final Rept Will Be Submitted Upon Completion of All Corrective Actions
GO2-82-549, Suppl to Final Deficiency Rept Re Spray Pond Leakage, Initially Reported 810610.Const Joint Between Floor Slab Sections & Foundation Being Repaired.Expansion Joints Replaced
GO2-82-470, Forwards Final Response to IE Bulletin 80-06, Engineered Safety Features (ESF) Reset Control. Minor Design Changes Identified & Will Be Completed Prior to Fuel Load
GO2-82-563, Final Deficiency Rept Re GE Control Switches SBM & SB-9, Initially Reported 820303.SB-9 Switches Determined Not Reportable Per 10CFR50.55e.SBM Swithces Installed in Class IE Electrical Applications Replaced
GO2-82-045, Forwards Interim Deficiency Repts for Reportable Conditions 175,WBG Radiographs & 177,bulk Purchase Valves
GO2-82-319, Submits Revised Response to NRC Re Violations Noted in IE Insp Repts 50-397/79-10 & 50-397/80-08. Corrective Actions:Piping post-weld Heat Treatment Will Follow Bechtel Procedures
GO2-82-318, Final Deficiency Rept Re Reverification of Weld Radiographs. Radiography Review to Be Completed by 820601.Filming of New Radiographs & Repair of Defective Welds Will Be Performed Per Turnover Schedule Priority
GO2-82-295, Final Deficiency Rept Re Bulk Purchase Valves Which Do Not Meet Full Design Requirements.Review Program to Be Completed in Sept 1982.All Deficiencies Will Be Corrected 90 Days Before Fuel Loading
GO2-82-143, Final Deficiency Rept Re Improper Matl Traceability for Concrete & Grouting,Initially Reported 801215.Recommends Sand Cement Grout Be Replaced
GO2-82-111, Final Deficiency Rept Re Out of Calibr Torque Wrenches.All Seismic Category 1 Drilled in Concrete Anchors Installed by 215 Contractor Will Be Retorqued & Identified by Torque Point
GO2-82-154, Final Deficiency Rept Re Number 161 Load Capacity Data Sheets,Initially Reported 810630.Data Sheets Obtained from Vendors.Evaluation of Catalog Loads Vs Certified Load Data Sheets for Each Type of Support & Vendor in Progress
GO2-82-112, Final Deficiency Rept Re Reportable Condition 155,concrete Anchor Failure Around Hanger Base Plates.Caused by Welding on Baseplates After Torquing.Event Isolated & Corrected & Therefore Not Reportable Under 10CFR50.55e
GO2-82-001, Interim Deficiency Rept Re Bulk Purchased Valves Installed in safety-related Sys Not Meeting Design Requirements. Extensive Evaluation & Review Program Being Conducted.Final or Updated Rept Will Be Submitted by 820308
GO2-81-055, Final Deficiency Rept Re Incorrectly Installed Class IE 250-volt Battery,Initially Reported 811202.New Battery Installation Will Be Purchased from Exide
GO2-81-052, Final Deficiency Rept Re Quality Class I Soil Backfill, Originally Reported on 811112.Extensive Test Program Using Penetration Tests,Downhole Nuclear Density & Pressuremeter Tests Concluded Item Is Not Reportable
GO2-81-051, Interim Deficiency Rept Re Load Capacity Data Sheets, Initially Reported 810630.Std Components Will Be Evaluated During Design Verification.Next Rept Will Be Submitted by 820211
GO2-81-491, Interim Deficiency Rept Requesting Extension of Reporting Date for 10CFR50.55(e) Reportable Condition 73 Re Concrete & Grouting Work,Initially Reported 811120.Final Rept Will Be Submitted by 820205
GO2-81-493, Final Deficiency Rept 144 Re Possible Installation of Defective 2-inch Schedule Pipe,Initially Reported on 811106. Extensive Testing Indicated That Piping Would Have No Adverse Effect on Plant.Condition Not Reportable
GO2-81-492, Final Deficiency Rept 80,re Pipe Weld ASME Defects,Initially Reported on 800319.Pipe Wall Thickness Was Less than Specified Min Wall But Above Code Required Thickness. Condition Determined Not Reportable Per 10CFR50.55e
GO2-81-045, Interim Deficiency Rept Re Possible Installation of Defective 2-inch Schedule 80 Pipe.No Evidence of Welds or Seams Observed.Further Insp & Testing Needed.Updated or Final Rept Will Be Provided by 811120
GO2-81-046, Interim Deficiency Rept on Potentially Reportable Condition 118 Re Spool Pieces Ape W/Wall Below Min Requirements.Tests of Surface Defects Will Be Completed by 811130.Final Rept Will Be Submitted by 811214
GO2-81-048, Interim Deficiency Rept Re out-of-calibr Torque Wrenches & Inability of Contractor Installation Procedure to Identify Which Safety or nonsafety-related Items Wrenches Used On. Final Rept & Corrective Action to Be Provided by 820205
GO2-81-047, Deficiency Rept Re Borg Warner Valves,Initially Reported 811020.Valves Thought to Have Wrong Type of Limitorque Installed But Review Concluded That Valves Are Properly Sized.Not Reportable Per 10CFR50.55e
GO2-81-414, Final Deficiency Rept Re Debris & Foreign Matl Identified in safety-related Sys,Initially Reported 810925.Cleanliness Insps Not Performed.Supply Sys Will Perform Audits/ Surveillances
GO2-81-043, Final Deficiency Rept Re Unqualified Motors in Limitorque Dc Valve Operators W/Class B Insulation,Initially Reported on 801030.Valve Operators Will Be Replaced W/Porter Peerless Dc Motors from Velan Valve Co & Anchor Darling
GO2-81-402, Interim Deficiency Rept Re Concrete & Grouting Work, Initially Reported 810817.Contractor to Supply Documentation on Grouting.Microcoring Test Program Being Developed.Final Rept by 811215
GO2-81-341, Responds to IE Bulletin 80-21 Re Valve Yokes Supplied by Malcolm Foundry Co,Inc.No Malcolm Foundry Components Used by Manufacturers or Contractors as Supply Source.Manpower Estimate & List of Manufacturers Encl
GO2-81-036, Final Deficiency Rept Re Nontestability of FA2 Logic, Initially Reported 810608.Describes Provisions to Be Taken for Nontestable Relay Which Are Reportable Per Part 21
GO2-81-032, Final Deficiency Rept Re Ultimate Heat Sink Spray Pond Leakage,Originally Reported on 810610.All Expansion Joints, Const Joints,Visible Cracks & Potential Leak Areas Will Be Filled W/Cement Based Chemical Sealant
GO2-81-336, Interim Deficiency Rept Re Out of Calibr Torque Wrenches, Initially Reported 810814.Review of Special Requirements Checklist for Sampling Bolted Installations Performed.Next Rept by 811120
GO2-81-246, Provides Final Response to IE Bulletin 79-03A, Longitudinal Weld Defects in ASME SA-312,Type 304 Stainless Steel Pipe. Etching Program on Effected Exposed Pipe Complete.No Evidence of ctr-line Lack of Weld Penetration
GO2-81-172, Interim Deficiency Rept Re Defective GE Type CR2940 Control Switches,Initially Reported on 810617.GE Has Completed Insp of Switches.Switches Not within GE Scope of Supply Will Also Be Inspected.Next Rept by 811001.Also Reported Per Part 2
GO2-81-018, Interim Deficiency Rept Re Coating/Painting Procedures, Initially Reported on 810612.Resubmittal of Wbg Subcontract/ Vendor Coating Procedures Will Commence on or Before 810803. Final Rept by 810901
GO2-81-019, Interim Deficiency Rept Re Anchor Failure Associated W/Welding Base Plates Fastened to Wall,Initially Reported 810623.Special Requirements Checklist Under Revision to Insure Adequacy of Requirements
GO2-81-020, Interim Deficiency Rept Re Load Capacity Data Sheets, Initially Reported 810630.Stress Repts to Be Reviewed for Adequate Design.Next Rept by 810918
GO2-81-140, Final Deficiency Rept Re Friction Clamps for Electrical Conduit,Initially Reported 810420.Inadequate Clamps Will Be Replaced or Addl Clamps Will Be Installed to Conduit or Tubing Runs
GO2-81-015, Interim Deficiency Rept,Originally Reported on 801030,re Limitorque Dc Valve Operator Motor W/Class B Insulation. Review Revealed Five Addl Unqualified Motor Operators. Motors Will Be Replaced Under Vendor Technical Guidance
GO2-81-021, Interim Deficiency Rept Re Steel Design Details for Small Bore Design Work,Initially Reported on 810417.Evaluation of Basic Design Criteria Completed & Std Support Details Are Being Revised.Final Rept by 810921
GO2-81-022, Interim Deficiency Rept Re Potentially Reportable Condition on Faz Logic Testability,Initially Reported 810708.Design Review Initiated.Next Rept by 811015
GO2-79-012, Updated Deficiency Rept Re Improper Installation of Concrete Anchors,Initially Reported on 790702.Specs & Procedures Revised to Provide Specific Installation & Insp Requirements
GO2-81-147, Potential Deficiency Rept Re Pipe Whip Restraints Inside Containment,Initially Reported on 810129.Deficiency Is Not Reportable.Overall Design Basis Modified
GO2-81-244, Updated Deficiency Rept Re Concrete & Grouting Work on Contract 215,initally Reported on 801114.Contractor Is Still Searching Records for Data on Grout in Question.Next Rept by 811023
GO2-81-024, Interim Deficiency Rept Re Out of Calibr Torque Wrenches, Originally Reported on 801215.Checklist Is Being Inserted Into Work Packages & Completion of Packages Will Be Done on Sys Priority Basis.Final Rept by 811005
GO2-81-017, Final Deficiency Rept Re HPCS Diesel Generator Air Start Motor & Piping Sys Not Protected by Relief Valves. Deficiency Not Reportable Because Failure of Air Starter Sys Represents Single Failure
GO2-81-203, Interim Deficiency Rept Re Quality Class I Hanger Details, Initially Reported on 810629.As-built Documents Are Being Completed on Sys Turnover Basis W/Completion Based on Final Sys Turnover.Final Rept by 811001
GO2-82-937, Interim Deficiency Rept 215 Re Skewed T-joint Welds. Initially Reported on 821022.Welds Lack Required Leg Length. Insp Sampling Plan Initiated for Large Bore Pipe Supports. Next Rept Expected by 830222
GO2-82-938, Final Deficiency Rept 216 Re RHR Relief Valve Vent.Initially Reported by Burns & Roe Under Part 21.Dual Reporting Not Required.Part 21 Repts Will Adequately Address Problem & Corrective Action
GO2-82-902, Forwards Updated Response to Revision 1 to IE Bulletin 82-01, Alterations of Radiographs of Welds in Piping Subassemblies. Final Rept Will Be Submitted When Work on Welds Completed
GO2-82-898, Final Deficiency Rept Re Incorrect Jones Control,Inc Instrumentation Piping Design.Initially Reported on 820720. Latest Thermal Displacement Data Will Be Maintained Up to Date
GO2-81-028, Final Deficiency Rept Re Inadequate Layup of Class I Piping Sys Following Hydrostatic Testing.Corrosion Due to Inadequate Layup Procedures Not Significant.Condition Not Reportable Under 10CFR50.55(e)
GO2-81-013, Final Deficiency Rept Re Gilbert/Commonwealth Use of Deficient Steel Design Details for Small Bore Design Work, Initially Reported 810417.Typical Load Ratings Revised to Meet Code Requirements
GO2-81-026, Updated Deficiency Rept Re Failure of Special Doors & Hatches to Perform Intended Function,Initially Reported 801114.Deficiencies Being Investigated.Next Rept Will Be Submitted by 811115
GO2-81-029, Updated Interim Deficiency Rept Re Problems Associated W/ Load Capacity Data Sheets,Initially Reported on 810630. Listing of WBG-purchased Hanger Component Not Having Load Capacity Data Sheets Encl.Next Rept by 811217
GO2-81-025, Final Deficiency Rept Re Incorrect Class Designation of Control Room Balance of Plant Panels,Initially Reported 810520.Investigation Has Determined Condition Not Reportable Under 10CFR50.55(e)
GO2-81-159, Interim Deficiency Rept Re Design Verification of Seismic Category I,Quality Class I Heating,Ventilation & Air Conditioning Sys Hangers,Originally Reported on 801215. Determined Condition Not Reportable Per 10CFR50.55e
GO2-81-162, Interim Deficiency Rept Re Failure in Testing Below Required Proof Load of Rigid Sway Strut Paddles.Site Engineering Performed Preliminary Review.Three Options Presented as Possible Solutions.Final Rept Will Be Submitted by 810918
GO2-80-160, Responds to IE Bulletin 81-02, Failure of Gate Type Valves to Close Against High Differential Pressure. No Subj Valves Obtained for Installation or as Spares.Approx 40 Manhours Expended
GO2-81-165, Interim Deficiency Rept Re Diesel Generator Bldg Heating Ventilation & Air Conditioning Sys Intake Ductwork Originally Reported 810417.Studies in Progress to Determine Suitable Prevention of Collapse of Ductwork
GO2-81-138, Interim Deficiency Rept,Originally Reported on 810209,re Ultimate Heat Sink Spray Pond Leakage.Caused Possibly by Wall Leakage.Water Levels Lowered by Pumping to 1/2 & 1/3 Full
GO2-81-148, Interim Deficiency Rept Re Control Room Balance of Plant Panel Quality & Seismic Class,Initially Reported on 810520. GE Evaluating Condition & Will Provide Review Results by 810705.Final Rept Will Be Provided by 810720
GO2-81-128, Responds to IE Bulletin 79-02,Revision 2, Pipe Support Base Plate Designs Using Concrete Expansion Anchor Bolts. Results of Analysis on Plate Flexibility Sampling Testing Work Will Be Issued in First Quarter of 1982
GO2-81-124, Deficiency Rept Re Defective Sway Brace Brackets,Initially Reported on 800820.All Defective Brackets Will Be Repaired &/Or Replaced.Design Load Allowables Will Be Derated
GO2-82-857, Forwards 12th Progress Rept Re Review of Completed safety-related Work,Per 800717 Commitments & Enforcement Action 80-20 Per Notice of Violation
GO2-83-073, Forwards Thirteenth Progress Rept Re Review of Completed safety-related Work for Oct - Dec 1982
GO2-82-385, Forwards Revised Corrective Actions to NRC Notice of Violations 79-10/01,79-10/03,80-09/09 & 80-08/22 Noted in IE Insp Rept 50-397/81-22.All Future Liquid Penetrant Exams Will Be Performed by Bechtel Approved Subcontractor
GO2-82-409, Revises 810904 Response to NRC Re Violations Noted in IE Insp Rept 50-397/81-03.Requests Extension to 820730 to Make Corrective Actions,Incorporating Changes Into Spec Control List & Drawing Control List
GO2-81-109, Responds to NRC Re Violations Noted in IE Insp Rept 50-397/81-05.Corrective Actions:Qa Program Nondestructive Testing Procedure for Magnetic Particle Insp Revised on 810415 to Indicate Partial Penetration Welds
GO2-81-122, Responds to NRC Re Violations Noted in IE Insp Rept 50-397/81-03.Corrective Actions:Deficient Items Reviewed & Scheduled for Updating as Required
GO2-81-120, Final Deficiency Rept Re Contract 215 Temporary Installation Program,Initially Submitted 810309.Contractor Will Use Insp Rept to Document & Control Temporary Installation.Condition Not Reportable Per 10CFR50.55e
GO2-81-121, Advises That Util re-evaluation of Mechanical Contractor WSH-Boecon-Geri Methods,Controls & Performance Has Been Completed.Improvements in Quality Program Assure Proper Work.Requests NRC Lift Stop Work Directive
GO2-81-106, Closeout Deficiency Rept Re Verification of Base Metal Thickness After Repairs,Originally Reported 801215.No Adverse Effect on Safe Plant Operation Noted.Condition Determined Not Reportable Per 10CFR50.55e
GO2-81-111, Interim Deficiency Rept Re Utilization of Deficient Std Design Details for Small Bore Supports Initially Reported on 810417.Re-evaluation of Basic Design Criteria Initiated. Final Rept to Be Submitted by 810731
GO2-80-310, Responds to IE Bulletin 80-23, Failures of Solenoid Valves Mfg by Valcor Engineering Corp. Specified Valves Are Not Used at Facility in safety-related Functions
GO2-81-119, Interim Deficiency Rept Re Annulus Pressurization on Piping Sys Attached to or Supported from Reactor Vessel or Sacrificial Shield Wall,Initially Reported 810122.Deficiency Found Reportable.Final Rept by June 1982
GO2-81-112, Final Deficiency Rept Re Thermite Welding on Buried Standby Svc Water Pipe,Initially Reported on 801222.No Adverse Effect on Plant Operation.Issue Determined Not Reportable Per 10CFR50.55(e)
GO2-80-290, Interim Deficiency Rept,Originally Reported on 801114,re Overloads on Supports for Spray Pond Piping.Caused by Hardware Design Error.Review of Original Design Margins to Be Completed by 801212
GO2-80-282, Interim Deficiency Rept Re Diesel Generator Switchgear Units DGI-7 & DG2-8 Installation.Caused by Insufficient Clearance Between Cabinets to Prevent Impact During Seismic Event. Switchgear Units Connected to Generator Control Cabinets
GO2-80-270, Forwards Full Payment in Response to NRC 801106 Amended Notices of Violation & Proposed Imposition of Civil Penalties.Evaluation & Corrective Action Program Initiated as Prerequisite to Addl safety-related Work
GO2-80-269, Forwards Response to NRC Re Violations Noted in IE Insp Rept 50-397/80-16.Corrective Actions:Const Deficiencies Reviewed for Reporting as Potential 10CFR.50.55e Items,Repts Submitted & Instruction Drafted
GO2-80-278, Final Deficiency Rept Re Fuel Pool Boiling Prevention, Initially Reported 770818.Addl Cooling Coils Will Not Be Placed in Standby Gas Treatment Sys.Corrective Action: Fuel Pool Cooling Sys Upgraded to Safety Grade Status
GO2-80-271, Interim Deficiency Rept Re Inadequacy of Sway Brace Brackets Mfg by Power Piping Co,Initially Reported on 800820.Caused by Undersized Welds & Poor Weld quality.In-plant Insp of Brackets Performed.Next Rept Is Scheduled for 810202
GO2-80-289, Interim Deficiency Rept Re Nonseismic Class 1 Const & Installation of Control Room Cabinet for Digital electro- Hydraulic Turbine Generator.Failure During Seismic Event Could Cause Damage to safety-related Equipment
GO2-82-945, Interim Deficiency Rept Re Controls for Remote Shutdown Panel & Pump Discharge Switch.Initially Reported on 820819 & 0820,respectively.Switches & Valves Will Be Relocated.Next Rept Will Be Submitted on 830228
GO2-82-905, Advises That IE Bulletin 82-01,Suppl 1 Re Itt Grinnell Supplied Matls,Is Not Applicable to Facility
GO2-82-049, Interim Deficiency Rept Re Excessive Voltage Drop Due to Long Control Cable Length,Initially Reported 820511.Possible Corrective Actions:Number 10 Rather than 12 Size Wire Used & CPT Size for Interposing Relay Increased
GO2-81-556, Forwards Suppl 2 to Engineering Evaluation of WNP-2 Sacrificial Shield Wall
GO2-81-027, Forwards Revised Response to NRC Re Violations Noted in IE Insp Rept 50-397/81-03.Corrective Actions: Personnel Responsible for Updating Drawings Retrained as of 810611