PLA-2476, Responds to Item 3 or Rev 1 to IE Bulletin 79-26.Computer Code Developed to Calculate Control Blade Depletion.No Control Blades Will Exceed 34% B-10 Depletion Averaged Over Upper 1/4 of Blade Before End of Second Cycle
PLA-2485, Forwards Audited Financial Statements & Other Financial Info for Nov 1983 - Oct 1984,in Accordance w/10CFR50.71
PLA-2471, Forwards Reactor Pressure Vessel Internals Steam Dryer Rept Summarizing Indications Found During Unit 1 Refueling Outage,Per Request.Indications Will Not Impact Safe Operation of Facility.Related Info Encl
PLA-2357, Forwards Rev 1 to Inservice Insp Program Plan & Response to 840912 Request for Addl Info on Program.Rev to Program Is Result of Addl Relief Requests Identified & Editorial Changes Deemed Necessary.Fee Paid
PLA-2114, Forwards Draft NUREG-1042, Tech Specs,Susquehanna Steam Electric Station
PLA-2138, Forwards Revs to FSAR Chapters 6,7 & 18.Revs Update Containment Isolation Provisions for Facilities & Will Be Incorporated in Annual FSAR Update in Jul 1984
PLA-2125, Forwards Amend 56 to Application for Class 103 Ol,Consisting of Rev 34 to FSAR
PLA-2095, Forwards Revised Response to Generic Ltr 83-28, Required Actions Based on Generic Implications of Salem ATWS Events, Reflecting Updates to Items 1.2.2,2.1,2.2.2 & 4.5
PLA-1940, Forwards Application for Amend 55 to Licenses NPF-14 & CPPR-102,consisting of Rev 7 to Emergency Plan
PLA-1934, Forwards Rev 1 to Preservice Insp Plan & Rev 0 to Preservice Insp Relief Request 8 Through 12,in Connection W/Ser Item 111
PLA-1827, Forwards Response to Generic Ltr 83-28, Required Actions Based on Generic Implications of Salem ATWS Events. Rept Will Be Revised to Reflect BWR Owners Group or INPO-NUTAC Responses
PLA-1795, Forwards Revised FSAR Sections 14.2.12.4 & 14.2.12.5 Covering Preoperational Test Program.Revs Will Be Incorporated in Next FSAR Amend
PLA-1870, Forwards Rev to Section 14.2 of FSAR Re Proposed Startup Test Program for Unit 2 & Clarification of Unit 1 Startup Test Program.Revs Will Be Incorporated Into Next FSAR Amend
PLA-1823, Forwards Rev 4 to Equipment Qualification Rept in Response to Items 1.9 & 3.11.1(1)a of Suppl 5 to SER & 10CFR50.49(i). Rev Represents Dynamic & Environ Qualification Program Status as of 830901
PLA-1785, Forwards Rev to FSAR Chapter 18 Reflecting Responses to TMI Items.Chapter Will Be Included in Next FSAR Amend
PLA-1698, Forwards Supplemental Response to SER Open Item 3.10.1(3). Fatigue Cycling Effects on NSSS Equipment Due to Safety Relief Loads (License Condition 23(a)) Discussed
PLA-1621, Forwards Response to Generic Ltr 82-33,Suppl 1 to NUREG-0737, Requirements for Emergency Response Capability. W/One Oversize Encl.Aperture Card Is Available in PDR
PLA-2514, Forwards Response to 850723 Request for Addl Info in Support of Tech Spec Exemption to Allow Diesel Generator Removal from Svc for 60 Days. Design Criteria,500 Kv Steel Pole Structure Transmission Lines, Encl
PLA-2475, Requests Deletion of Nd Weiss & Eb Poser from Svc List & Addition of Rj Benich
PLA-2472, Responds to 850319 Request for Addl Info Re Responses to Generic Ltr 83-28,Items 2.1,2.2.2 & 4.5.3.Testing of Backup Scram Valves at Refueling Outage Frequency Added to Preventative Maint Program
PLA-2440, Forwards Application for Proposed Amends 66 & 19 to Licenses NPF-14 & NPF-22,respectively.Amends Change Tech Specs to Support Operation W/One Recirculation Loop Out of Svc.Fee Paid
PLA-2443, Submits Actions Taken in Response to Findings Resulting from NRC Review of Fire Protection Program & Fire Hazards Analysis During Wk of 850318.Control Room Panels Will Be Reanalyzed.Summary of Analysis Will Be Submitted by 850624
PLA-2407, Forwards Applications for Proposed Amends 63 & 17 to Licenses NPF-14 & NPF-22,respectively,revising Membership of Util Review Committee.Fee Paid
PLA-2370, Forwards Applications for Proposed Amends 57 & 12 to Licenses NPF-14 & NPF-22,respectively.Amends Change Tech Specs to Separate Unit 1 & 2 Battery Loads to Avoid Forced Shutdown of Unit 2 During Unit 1 Refueling Outage
PLA-2354, Submits Additions & Corrections to Svc List for Facility. W Matson Should Be Added to List.We Barberich Title Should Be Corrected to Manager of Nuclear Licensing
PLA-2210, Responds to Generic Ltr 84-11, Insp of BWR Stainless Steel Piping. Induction Heating Stress Improvement & Ultrasonic Testing or Radiography Will Be Performed on Unit 1 Welds During First Refueling Outage
PLA-2142, Amends Response to FSAR Question 110.57,per 840319 Telcon. Visual Insp on Unit 1 Lines Revealed No Appreciable Vibratory Effects.Fsar Rev,Reflecting Position,Will Be Provided
PLA-2109, Clarifies Cover Ltr to Rev 7 to Emergency Plan (PLA-1940). Details Provided for Manning Emergency Operation Facility (EOF) & Activation of Backup Eof.Unit 2 Fuel Load Scheduled for 840326.Expeditious Approval Requested
PLA-2134, Requests That Further Action on BWR Core Thermal Hydraulic Stability Be Deferred,Due to Lack of Time to Review New Info Presented at 840308 Meeting W/Nrc
PLA-2060, Responds to Inquiry Re Feedwater Piping Outside Reactor Bldg.Main Steam Piping Runs Through Turbine Bldg Main Steam Pipe Tunnel,Resulted in Total Separation from Feedwater Piping in Area
PLA-2059, Provides Revised Scheduled Completion Date for Safety Parameter Display Sys of No Later than 840701.Extending Completion Date Will Not Reduce Ability to Deal W/Emergency
PLA-2052, Requests Exemption from 10CFR50,App E Requirement for State & Local Govt Full Offsite Participation in Emergency Planning Exercise
PLA-1879, Requests Approval of ASME Code Case N-253-2, Const of Class 2 or 3 Components for Elevated Temp Svc Section III, Div I, for Application to Diesel Engine Exhaust Gas Expansion Joint for Addl New Diesel Generator
PLA-1820, Forwards Revised FSAR Section 7.4 Changing Pressure at Which Reactor Shutdown Cooling Sys Will Operate.Rev Will Be Incorporated Into Next FSAR Amend
PLA-1821, Forwards Revised FSAR Section 7.1.New Section 7.1.2.6.9 Added to Provided Ref to Compliance W/Reg Guide 1.45. Sections 7.1.2.6.9-7.1.6.20 Renumbered & Section 7.1.2.5.21 Provides Ref to Position on Reg Guide 1.97
PLA-1738, Responds to Re Assessment & Consequences of Immediate or Delayed Gas Cloud Ignition Resulting from Rupture of Transco Pipeline.Heat Flux Does Not Pose Safety Concern
PLA-1716, Responds to Ser,Suppl 5,Item 3.11.1(1)(a) Re nonsafety- Related Electrical Equipment.Failure of nonsafety-related Equipment Unlikely Due to Classification Under Qualification Program
PLA-1557, Discusses Final Results of Addl Test of Adequacy of Design Process.Audit to Verify Test Results Confirms Design Adequacy
PLA-1499, Comments on Physical Security Plan Re Security Officer & Detectors in Response to NRC .Encl Info Will Be Included in Change N to Plan Which Will Be Submitted in Feb 1983
PLA-1479, Forwards Enlarged Photographs Showing Two Different Site Views to Complete Nomination of Historic Places Forms Submitted on 821109
PLA-1390, Forwards Natl Registry of Historic Places Inventory Nomination Forms for Riverlands Recreation Area,Luzerne County,Pa
PLA-1298, Forwards Responses to NRC Questions Re Small Bore Pipe. Twelve Oversize Drawings Encl,Including Three Illegible. Aperture Cards Are Available in PDR
PLA-1254, Responds to SER Suppl 3 Section 3.11.5(2)(a) Re Qualification Updates,Revised Justifications for Interim Operation & Addl Info Required Prior to Exceeding 5% Power. Harsh Environ Class IE Equipment Addressed
PLA-1228, Forwards Updated Preservice Insp Program Info Re SER Issue 19.Revision Includes Preservice Exams Performed Subsequent to Util 810519,0616 & 820523 Submittals
PLA-1164, Responds to Structural Engineering Branch Questions Re Vertical Dynamic Analysis,Discussed During 820629 Meeting & 0630 Telcon.Drawings of Diesel Generator Bldg Floor Plan & Structural Steel Encl
PLA-1159, Informs That Revised Seismic Response Spectra,Resulting from Recent Vertical Dynamical Model Assessment,Will Be Incorporated in Design Work Specs by End of 1982
PLA-1161, Informs That Schedule for Gas Pipeline Revised.Analysis Will Be Complete by Feb 1983.Physical Configuration Changes Will Be Implemented by Sept 1984
PLA-1084, Forwards Environ Qualification Justification for Interim Operation of Class IE Equipment Per NUREG-0588.Tech Specs Meet Qualifications Contained in Generic Ltr 82-09
PLA-1036, Informs of Completion of Technical Evaluation of Excess Flow Check Valves,Sensing Lines & Valve Testability Requirements. Lines Tested Per ASME Section III Class 2.Valves Open to Containment or Suppression Pool Listed
PLA-2529, Forwards Fire Protection Program Summary Repts Re Unrated Fire Zone Boundaries & Associated Circuits within Control Room & Evaluation of Selected Fire Doors & Door Frame Assemblies W/Suppl 1.W/two Oversize Drawings.Fee Paid
PLA-2314, Forwards Application for Amend 50 to License NPF-14.Amend Revises Tech Specs Re Min Channels Operable & Measurement Range Requirements.Approval within 30 Days Requested
PLA-2293, Forwards Application to Amend License NPF-14,revising Tech Specs Re Removal of 50-degree Blocking Requirements,Per NUREG-0737,Item,II.E.4.2,rev of Isolation Times & Rev of Bases for Consistency W/Unit 2 Bases
PLA-1894, Forwards Rev 1 to Control Sys Power Supply & Sensor Malfunction Study. Existing Sys Adequately Controls Facility
PLA-1789, Forwards Allegheny Electric Cooperative,Inc Annual Financial Rept FY82
PLA-1350, Forwards Application for Amend 10 to License NPF-14,changing Tech Spec Table 3.8.4.1-1 to Include More Conservative Type 2 Molded Case Circuit Breakers & to Add Previously Omitted Type 3 Molded Case Circuit Breakers
PLA-1250, Forwards Qualification Fire Test of Protective Envelope Sys, Per License Condition 7.Results Show Adequacy of Tested Wrapping Matl of as-installed 1-h Cable Wrap Configuration
PLA-1232, Forwards Results of Vacuum Breaker Performance Evaluation Providing Justification for Plant Operation Beyond Mode 3. Draft NEDE-22178-P, Mark II Containment Drywell-to-Wetwell Vacuum Breaker Models, Withheld (Ref 10CFR2.790)
PLA-1111, Forwards Info in Response to NUREG-0737,Item II.E.4.2 Re Containment Vent & Purge Valves.Several Valves Do Not Meet Required Closing Time.Investigation Underway.Info Closes SER Item 84
L-77-002, Letter Responding to IE Bulletin No. 77-02 and Advising That a Full Response Will Be Available About January 30, 1978
PLA-1687, Interim Deficiency Rept Re Potential Excessive Offsite Dose Concerning Feedwater Containment Penetrations Not Maintaining Water Seal for 30 Days post-LOCA.Also Reportable Under Part 21
PLA-1652, Interim Deficiency Rept Re Failure of GE Reactor Mode Switch to Actuate Reactor Protection Sys Channel.Initially Reported on 830407.Franklin Inst Test & Analysis Rept on 830322 Switch Failure Encl.Final Rept for Unit 2 by 831001
PLA-1459, Forwards Dynamic Qualification Summary Package & GE Final Test Rept, NEDC-22177.GE Rept Withheld (Ref 10CFR2.790)
PLA-1295, Final Deficiency Rept Re Potential Failure of Agastat E7000 Relays.Initially Reported on 820217.During 820223-24 Visual insp,63 Relays Determined faulty,52 Returned to Manufacturer & 11 Placed on Defective Device List
PLA-2478, Forwards Final Qualification Repts for Power Range Monitor Cabinet & HPCI Turbine.Facility Fully Qualified to Sqrt Criteria.Repts Withheld
PLA-1035, Forwards Public Version of Revised Emergency Plan Implementing Procedures,Including Procedures EP-IP-001 Re Emergency Classification & EP-DP-002 Re Emergency Mgt Notification.Receipt Form Encl
PLA-1082, Forwards Amend 46 to OL Application,Including Revision K to Security Plan.Plan Revision Withheld (Ref 10CFR2.790)
PLA-1076, Final Deficiency Rept Re Defects in Welds of Recirculation Pump Support Lugs,Initially Reported on 820326.Welds Removed & Repaired on All Three Lugs on a & B Pumps.Also Reportable Per Part 21
PLA-1065, Revises 800911 Submittal in Response to IE Bulletin 79-14, Seismic Analysis for As-Built Safety-Related Piping Sys. Const Will Be Completed by 820601
PLA-1049, Final Deficiency Rept Re Rosemount Models 1151 & 1152 Pressure Transmitters W/Type a or D Electronics Containing Amplifier Boards W/Potentially Defective Zener Diodes, Initially Reported 820410.Transmitters Replaced
PLA-1037, Responds to IE Bulletin 79-27, Loss of Non-Class IE Instrumentation & Control Power Sys Bus During Operation. Addl Info Re Power Distribution Buses Suppls 810213,0601, 0828 & 1021 Transmittals.Response Complete
PLA-1025, Comments on Proposed Revision 2 to Reg Guide 1.105 Re Instrument Setpoints.Draft Documents Should Not Be Endorsed Due to Temporary Nature of Matl
PLA-1028, Final Deficiency Rept Re Improper Orientation of Back Draft Isolation Dampers,Initially Reported 810603.Improperly Oriented Dampers Identified & Orientation Corrected.Unit 1 Work Completed.Unit 2 Pending.Also Reported Per Part 21
PLA-1027, Final Deficiency Rept Re Violation of Separation/Isolation Criteria for Class IE Electrical Equipment.Procedure FP-E-10 & Drawings E-396 & E-60 Developed to Reflect Current SAR Commitments.Also Reported Per 10CFR21
PLA-1032, Part 21 Rept Re Existence of Goldfish in Spray Pond, Initially Reported 820303.Goldfish Elimination Will Be Completed Prior to Summer 1982.Util Will Periodically Examine Pond to Preclude Reintroduction of Fish Population
PLA-1011, Final Deficiency Rept Re Limitorque Valve Operator Motor Shaft to Pinion Gear Keys,Initially Reported 810817 Per IE Info Notice 81-08.Affected Keys in Smb 3,4 & 5 Operators to Be Replaced & Design Change Package 552,Revision 1,issued
PLA-1005, Updated Interim Deficiency Rept Re Failure of Reactor Core Isolation Cooling Turbine Exhaust Swing Check Valve, Initially Reported 810410.Also Reported Per Part 21
PLA-1007, Final Deficiency Rept Re Inadequate Thickness of Main Steam Relief Valve Discharge Line Flanges,Initially Reported 811009.Caused by Failure of Vendor to Provide Flanges of Proper Thickness Consistent W/Certificate of Compliance
PLA-1001, Final Deficiency Rept Re Failure of American Insulated Wire Corp 600-volt Cable,Originally Reported on 810901.Caused by Gradual Breakdown & Embrittlement of Matl.All Cable Replaced W/Boston Insulated Wire Cable.Also Reported Per Part 21
PLA-1105, Responds to IE Bulletin 82-01,Revision 1, Alteration of Radiographs of Welds in Piping Subassemblies. Util Performed 100% Insp of 408 Radiographs & Reader Sheet Records.No Discrepancies Found
PLA-1066, Final Deficiency Rept Re Loose Mounting Screws on GE Type CR2940 Selector Switches,Initially Reported on 800924. Selector Screws Inspected & Improperly Torqued Screws Tightened.Also Reported Per Part 21
PLA-1083, Responds to NRC Re Violations Noted in IE Insp Rept 50-387/82-08.Corrective Actions:Training Session to Be Held & Technician Counseled Re Administrative Control Mechanisms
PLA-1089, Forwards Ecological Studies of Susquehanna River in Vicinity of Susquehanna Steam Electric Station, 1981 Annual Rept
PLA-1125, Forwards Amend 48 to Application for Ol,Requesting Issuance of OLs for 40-yr Period & Updating Directors & Principal Officers Lists to Reflect Personnel Changes
PLA-1097, Forwards Addl Info in Response to NRC Concerns Re Chugging Load Definition.Info Will Be Incorporated Into Design Assessment Rept Scheduled for Submittal on 820608
PLA-2118, Final Part 21/deficiency Rept Re Clamps on CRD Insert/ Withdrawal Lines.Initially Reported on 831209.Outer Pedestal Modified Due to Lack of Sufficient Axial Restraint Capacity of Inner Pedestal Support
PLA-1902, Interim Deficiency Rept Re Isolation of Nitrogen Makeup Sys. Also Reportable Per Part 21.Initially Reported on 830912. Permanent Design Mod Will Be Implemented.Final Rept Will Be Submitted in Dec 1983
PLA-1812, Final Deficiency Rept Re Water Hammer in Essential Svc Water Sys.Initially Reported on 830505.Vacuum Breakers Will Be Installed During First Refueling Outage.Also Reported Per Part 21
PLA-1872, Second Interim Deficiency Rept Re GE Reactor Mode Switch. Initially Reported on 830407.Mode Switch Redesigned.Sample Will Be Independently Tested.Also Reported Per Part 21.Final Rept Will Be Submitted by Dec 1983
PLA-2230, Final Deficiency Rept Re Electrical Separation Inside Multiple Div Junction & Pull Boxes.Initially Reported on 830721.Drawings Revised to Clarify &/Or Define Sparation Requirements for Use W/Junction & Pull Boxes
PLA-2074, Third Interim Deficiency Rept Re Electrical Separation Inside Multiple Division Junction & Pull Box.Initially Reported on 830721.Design Basis Criteria & Barrier Configuration Established.Also Reported Per Part 21
PLA-2137, Revised Final Deficiency Rept Re Fraying of Hydrogen Recombiner Cables.Initially Reported on 830728.Fraying Caused by Handling Process for Shipment,Installation & Testing.Cables Repaired
PLA-2130, Completes Response to IE Bulletin 83-07, Apparently Fraudulent Products Sold by Ray Miller,Inc & Two Suppls. No Ray Miller,Inc Matl Installed.Nuclear Energy Svc,Inc Supplied Ultrasonic Calibr Blocks
PLA-2089, Final Deficiency & Part 21 Repts Re Safety Parameter Display Sys Technology Energy Corp Model 156 Isolators.Initially Reported on 840106.Non-IE Power Supply Will Be Provided for Isolator Prior to End of First Refueling
PLA-2103, Final Deficiency Rept Re Cavitation of Jet Pumps Due to Induction Heating Stress Improvement Cooling.Initially Reported on 831206.No Erosion Found.Also Reportable Per Part 21.Item Not Reportable Per 10CFR50.55(e)
PLA-2084, Responds to IE Bulletin 83-08.Circuit Breakers W/ Undervoltage Trip Attachments Not Used in safety-related Applications in Unit 1.Subj Attachments Installed in Unit 2 Will Be Removed from safety-related Applications
PLA-2073, Final Part 21 Rept Re Hydrogen Catalyst Used in Comsip Custom Line Model K-IV Containment Gas Monitoring Panels. Initially Reported on 840113.Comsip Redesigned Catalyst Will Be Installed
PLA-2062, Final Deficiency Rept Re Bechtel Failure to Accomplish Design Verification of safety-related Power & Control Cables.Caused by Failure to Complete Required Cable Length Verification.Deficiency Not Reportable Per 10CFR50.55(e)
PLA-2180, Final Part 21/deficiency Rept Re Improper Relief Valve Settings,Design Pressures & Temps.Initially Reported on 831118.Calculations Performed Assure Lines Adequate for Intended Svc
PLA-2140, Second Interim Deficiency Rept Re Base Metal Cracking in Angle Fittings.Initially Reported on 840206.Angle Fittings Added to Defective Device List & Conduit Installation Spec Revised.Also Reportable Per 10CFR21
PLA-2149, Forwards Proprietary Final Rept, Susquehanna Unit 2 Jet Pump Cavitation Vibration Measurements. Rept Withheld (Ref 10CFR2.790)
PLA-2000, Interim Deficiency Rept Re Electrical Sys Separation in Multiple Div Pull & Junction Boxes.One Box Identified Containing Redundant Channel C & D Circuits Insufficiently Separated by Approved Barrier
PLA-1990, Final Deficiency Rept Re Isolation of Nitrogen Makeup Sys. Permanent Mod Consists of Rerouting Drywell & Wetwell Nitrogen Makeup Lines to Spare Penetrations.Divisionalized Isolation Valves Will Be Installed
PLA-1991, Final Deficiency Rept Re Cracks in Pacific Scientific PSA-1 & PSA-3 Snubber Capstan Springs.Caused by Improper Spring Forming.Snubbers Will Be Corrected Prior to Completion of First Refueling Outage.Also Reported Per Part 21
PLA-1946, Interim Deficiency Rept Re Bechtel Failure to Accomplish Design Verification of safety-related Power & Control Cables.Bechtel Completed & Documented Required Cable Length Verification & Calculations
PLA-1968, Final Deficiency & Part 21 Repts Re Final Design of GE 7700 Series 250-volt Dc Control Ctrs.Plant Operating Procedures Revised to Include Methods of Clearing Obstructions as Provided by GE & Exam & Reforming of Draw Out Contacts
PLA-1967, Final Deficiency Rept Re Suppression Pool Temp Monitoring Sys (Spotmos).Initially Reported on 821015.Modified Installation Configuration Tested.Review of Test Results Will Be Completed by End of Mar 1984
PLA-1987, Updated Interim Deficiency Rept Re Scram Discharge Vol Vent & Drain Valve Waterhammer.Testing & Subsequent Analysis Will Be Completed in Mar 1984.Util Will Submit Final Rept by Apr 1984
PLA-1973, Final Deficiency Rept Re Insufficient Corrosion Allowance for Essential Svc Water Piping to & from RHR Pump Motor Oil Coolers.Initially Reported on 831102.Piping to Be Replaced. Also Reported Per Part 21 for Unit 2
PLA-1928, Revised Deficiency Rept Re Anchor/Darling Valve Co Globe Valves Used in Throttling Svc within RHR Sys.Initially Reported on 811112.Listed Interim Measures Adequate Until Permanent Mods Implemented
PLA-1924, Interim Part 21 Rept Re Cavitation of Jet Pumps Due to Induction Heating Stress Improvement Cooling.Initially Reported on 830621.Caused by Inadequate Precautions to Prevent Cavitation Area Operation
PLA-1914, Final Deficiency Rept Re Lack of Movement in Itt Grinnell Snubber Brackets.All Snubbers Will Be Capable of + or -5 Degree Movement Per Rear Bracket Design.Reinsp Documented on Bechtel Nonconformance Rept 10809.Also Reported Per Part 21
PLA-1925, Final Deficiency Rept Re Spray Pond Siphoning Through Makeup/Deicing Line.Initially Reported on 830805.Spray Pond Operating Limits Will Be Changed to Require Min Spray Pond Inventory of 23 Million Gallons.Also Reported Per Part 21
PLA-1883, Interim Deficiency Rept Re Electrical Sys Separation Inside Multiple Div Pull Boxes & Junction Boxes.Walkdown/Insp Results Being Analyzed.Final Rept Will Be Submitted in Nov 1983
PLA-2094, Forwards Proposed Change to Physical Security Plan & Proposed Amend 37 to License NPF-14.Amend Revises Physical Security Plan & License Condition 2.D.Plan Change Withheld (Ref 10CFR2.790)
PLA-2045, Followup Deficiency Rept Re Mod of RHR Globe Valves F017A & FO17B to Enable Valves in Shutdown Cooling Mode to Perform W/O Adverse Cavitation & Vibration at Low Flow Rates.Initially Reported on 811112.Valves Replaced
PLA-2026, Interim Deficiency Rept Re GE Reactor Mode Switch.Proposed Redesign of Mode Switch by GE Rejected,Based on Results of Testing Conducted at Franklin Inst Research Lab.Alternate Switch Ordered Through Electroswitch.Final Rept by Apr 1984
PLA-1648, Forwards Application for Amend 54 to OLs Containing Rev 33 to FSAR
PLA-2009, Final Deficiency Rept Re Standby Gas Treatment Sys (SGTS) Performance Not as Described in Fsar.Fsar Change Prepared to Indicate SGTS May Be Required to Maintain Secondary Containment Integrity
PLA-1439, Interim Deficiency Rept Re Design Verification of Max Permissible Lengths of Wire in Low Voltage Power & Control Circuits.Caused by Bechtel Failure to Follow Procedures. Final Rept by 830415.Also Reportable Per Part 21
PLA-1436, Final Deficiency Rept Re Nonconformance of Bechtel Field Welding.Initially Reported on 821115.Training Sessions Conducted Re Welding QC Requirements & Procedures FP-G-24 & FP-W-1 Will Be Revised.Also Reported Per Part 21
PLA-1106, Interim Deficiency Rept Re Inconsistencies in Vertical Dynamic Model for Reactor/Control Bldg.Stress Analysis of Typical Floor Slabs & Supporting Beams Showed Adequate Margin to Ensure Integrity.Next Rept Before Fuel Load
PLA-1100, Final Deficiency Rept Re Inadequate Design & Welding of Horizontal Bracing Sys for Primary Containment Vent Pipes, Initially Reported 810603.Bracing Sys Rearranged & Documented on Drawing E-105361.Also Reportable Per Part 21
PLA-1816, Interim Deficiency Rept Re Potential for Siphoning Portion of Min Spray Pond Inventory.Initially Reported on 830805. Corrective Action Still Under Consideration.Final Rept Will Be Submitted in Oct 1983.Also Reportable Per Part 21
PLA-1797, Final Deficiency & Part 21 Repts Re Insufficient Clearance W/Ge Hma Auxiliary Relays.Initially Reported on 830119. Evaluation Concluded Deficiency Not Reportable Per 10CFR50.55(e).Relays Reworked
PLA-1807, Final Deficiency Rept Re Westinghouse Hydrogen Recombiners W/O Bushings to Protect Power Cables.Initially Reported on 830728.Cables Wrapped W/Glass Cloth Tape & Stainless Steel Flex Conduit.Also Reportable Per Part 21
PLA-1799, Interim Deficiency Rept Re Tipping in GE 7700 Line 250-volt Dc Control Ctrs.Initially Reported on 830721.GE Will Inspect Control Ctrs.Final Rept Will Be Submitted by End of Nov 1983.Also Reportable Per Part 21
PLA-1765, Final Deficiency Rept Re Feedwater Bypass Leakage & Potential Excessive Offsite Dose.Util Will Evaluate Sys Mods to Restore Original Design.Fsar Will Be Revised to Reflect Any Required Changes.Also Reported Per Part 21
PLA-1762, Interim Deficiency Rept Re Scram Discharge Vol Vent,Drain Valve & Water Hammer Loads.Initially Reported on 830628. Performance of Analysis to Determine Load & Impact Underway. Also Reported Per Part 21
PLA-1754, Final Deficiency Rept Re Improperly Torqued Shock Suppressor Screws on Piping Sys.Initially Reported on 830622.Screws Retorqued.Bechtel Field Procedure FP-P-20 Revised to Delineate Torque Values.Also Reported Per Part 21
PLA-1749, Interim Deficiency Rept Re Cavitation of Jet Pumps Due to Induction Heating Stress Improvement Cooling.Initially Reported on 830621.Preliminary Vibration Tests Performed. Also Reportable Per Part 21.Final Rept to Be Issued by Oct
PLA-1748, Second Interim Part 21 Rept Re Inadequacies in Bechtel Design Verification of Max Circuit Lengths of Low Voltage Power & Control Cables.Initially Reported on 821215.Next Rept by 831031
PLA-1737, Final Deficiency Rept Re Detachment of Ilsco Corp Number 14 Stranded Wire from Screw Clamp Detectors.Initially Reported on 830524.Deficiency Not Reportable Per 10CFR50.55(e) for Unit 2.Item Reportable Per Part 21 for Unit 1
PLA-1798, Interim Deficiency Rept Re Electrical Separation Inside Multiple Div Junction & Pull Boxes.Initially Reported on 830721.Final Design Basis Criteria to Be Set.Next Rept by Sept 1983.Also Reportable Per Part 21 for Unit 2
PLA-1638, Submits Addl Info Re IE Bulletin 82-01,Rev 1,Suppl 1, Alterations of Radiographs of Welds in Piping Subassemblies, Per 830330 Request.Three Radiographs Dispositioned Per PSI Ultrasonic Exam,Asme Code Section XI
PLA-2215, Final Deficiency Rept Re Base Metal Cracking & Bending of Angle Fittings Mfg by Unistrut,Powerstrut & B-Line Used on Class IE Electrical Raceways & Category 1 HVAC Supports. Initially Reported on 840206.Spec Revised
PLA-2006, Interim Part 21 Rept Re Improper Relief Valve Settings & Design Pressures & Temps Found in Hpci,Rcic,Rhr,Core Spray & Essential Svc Water Sys.Initially Reported on 831118. Hydrotests Performed
PLA-2063, Interim Part 21 Rept Re Safety Parameter Display Sys Model 156 Isolators Mfg by Technology for Energy Corp (Tec). Initially Reported on 840106.All Tec Isolators Reviewed for Corrective Actions
PLA-2033, Interim Deficiency Rept Re Clamps on Control Rod Drive Insert/Withdraw Lines Not Providing Axial Restraint. Initially Reported on 831209.Design Mod to Pedestal Support Initiated.Also Reportable Per Part 21
PLA-1703, Interim Deficiency Rept Re Defective GE Hma Auxiliary Relays.Insp Program Completion Awaiting Receipt of GE Recommended Corrective Actions.Final Rept Scheduled for 830901
PLA-1701, Application to Amend License NPF-14,consisting of Proposed Amend 25 to Revise Physical Security Plan to Include Changes N,O & P & Changes a & B to Security Training & Qualification Plan.Change P Withheld (Ref 10CFR73.21)
PLA-1677, Interim Deficiency Rept Re Lack of Movement in Itt Grinnell Snubber Brackets.Initially Reported on 830429.All Snubbers Will Be Reinspected & Design & Installation Processes Under Review.Final Rept Due Oct 1983.Also Reported Per Part 21
PLA-1666, Forwards Equipment Qualification Summary Rept.Summary Info Submitted Complete for Unit 1 But Only Partially Complete for Unit 2.Next Rev of Rept Will Contain Complete Info for Unit 2
PLA-1541, Correction to Interim Deficiency Rept Re Potentially Defective GE Hma Relays.Recorded Date for Ltr PLA-1528 Is 830218
PLA-1528, Interim Deficiency Rept Re Defective GE Hma Auxiliary Relays Resulting in Insufficient Clearances Between Armature Tail Piece & Molded Posts.Initially Reported on 830119.Final Rept by 830601.Also Reported Per Part 21
PLA-1527, Forwards Change B to Security Training & Qualification Plan. Change Withheld (Ref 10CFR2.790)
PLA-1509, Final Deficiency Rept Re Inadequate Restraint Provided by Pipe Friction Clamp Anchors.Initially Reported on 820723. Drawings Revised & Previously Accepted Friction Clamps to Be Reinspected & Reworked.Also Reported Per Part 21
PLA-1508, Final Deficiency Rept Re Inadequacies W/Design,Mfg & Installation of Pacific Scientific Shock Suppressors & Associated Itt Grinnell Clamps.Initially Reported on 820820. Specs & Procedures Revised.Also Reported Per Part 21
PLA-1282, Responds to IE Bulletin 82-01,Revision 1,Suppl 1.Review of 22,680 Unit 1 & Common Radiographs & 18,250 Unit 2 Radiographs Performed on 4,310 Vendor Welds.Corrective Actions for Unit 1 & Common Nonconformances Implemented
PLA-1534, Updated Final Deficiency Rept Re Defects in Agastat GP Series Relays.All safety-related Relays,Except Relays in Diesel Generator Panels,Replaced W/New Qualified Relays
PLA-1150, Responds to 820604 Systematic Assessment of Licensee Performance.Items Discussed Include Licensed Operators, Health Physics & Chemistry Staffs,Operating Procedures, Punch List Status & Open Items
PLA-1340, Final Deficiency Rept Re Pump Motor Start Times for Emergency Svc Water,Core Spray & RHR Sys.Initially Reported on 820910.Low Pressure Vessel Interlock Deleted from RHR & Core Spray Pump Start.Also Reported Per Part 21
PLA-1341, Final Deficiency Rept Re Improper Field Mounting of Agastat 7000/E7000 Relays.Initially Reported on 820702.Corner Mounted Screws & Relays Will Be Reworked by 821026.Also Reported Per Part 21
PLA-1296, Forwards Description of Actions to Be Taken to Correct Deficiencies in Physical Security Plan,Per 820901-02 Discussions.Revised Plan Forthcoming.Encl Withheld (Ref 10CFR73.21)
PLA-1306, Interim Deficiency Rept Re Inadequate Clearance in Pacific Scientific Shock Suppressors & Itt Grinnell Pipe Clamps. Initially Reported on 820820.Final Rept Will Be Submitted by 830201.Also Reported Per Part 21
PLA-1513, Final Deficiency Rept Re Defects in Byron-Jackson Recirculation Pump Lug Welds.Initially Reported on 830106. Welds Repaired & Liquid Penetrant Examined.Also Reported Per Part 21
PLA-1429, Responds to NRC Re Violations Noted in IE Insp Rept 50-387/82-36.Corrective Actions:Nde Level III Radiographic Film Interpreters re-reviewed 3,000 Radiographs.Six Welds Reworked Successfully
PLA-1273, Final Deficiency Rept Re Incorrect Wipe Setting of Normally Closed Contacts on Hfa Relays.Initially Reported on 820813. All safety-related Hfa Relays for Unit 2 Checked & Recalibr. Also Reported Per Part 21
PLA-1277, Interim Deficiency Rept Re Inadequate Restraint Provided on Pipe Friction Clamp Anchors.Initially Reported on 820723. Final Rept Pending Receipt & Review of Bechtel Assessment
PLA-1236, Final Deficiency Rept Re Error in Backpressure Calculations for Main Steam Safety Relief Valve Adjusting Ring Settings. Initially Reported on 820714.GE Corrected Calculational Error.Also Reported Per Part 21
PLA-1205, Final Deficiency Rept Re Inconsistencies in Vertical Dynamic Model for Reactor/Control Bldg.Initially Reported on 820426.Deficiency Determined Not Reportable Per 10CFR50.55e. Reporting Responsibilities Per 10CFR21 Satisfied
PLA-1146, Responds to NRC Re Violations Noted in IE Insp Rept 50-387/82-09.Corrective Actions:Audit of Startup Work List Conducted to Verify Compliance W/Requirements of Startup Administrative Manual
PLA-1223, Interim Deficiency Rept Re Improper Field Mounting of Agastat 7000/E7000 Series Relays.Initially Reported on 820702.Investigation Underway.Relays Will Be Reworked to Ensure Conformance.Also Reported Per Part 21
PLA-1196, Forwards Amend 50 to OL Application,Containing Revision 1 to Facility Security Plan.Encl Withheld (Ref 10CFR2.790)
PLA-1198, Final Deficiency Rept Re Inability of Crosby Safety Relief Valve Solenoids to Actuate at Postulated Reduced Dc Sys Voltages,Initially Reported 810801.New Solenoid Pilot Valves Installed
PLA-1154, Final Deficiency Rept Re RHR Pump Starting Voltage Limit Exceeding Tech Specs,Initially Reported 820525.Mods Implemented to Ensure Availability of Min Starting Voltage During Sequencing.Also Reported Per Part 21
PLA-1162, Final Deficiency Rept Re Failure of QC-inspected & Accepted Pipe Support Welds to Meet Requirements of Bechtel Spec 8856-M-213,initially Reported 810608.Welds Will Be Reworked or Technically Justified
PLA-1130, Responds to NRC Re Violations Noted in IE Emergency Preparedness Appraisal Rept 50-387/82-12. Corrective Actions:Training for Two Addl Emergency Operations Facility Support Managers 90% Complete
PLA-1129, Interim Deficiency Rept Re Emergency Svc Water Sys Water Hammer,Initially Reported on 820505.Condition Being Reviewed & Corrective Action Plan Will Eliminate Problem Associated W/Water Hammer in Emergency Svc Water Sys
PLA-1099, Final Deficiency Rept Re Cutler-Hammer Size 2 Motor Starters,Initially Reported 810819.All Size 2 Ac Motor Starters Checked to Verify Absence of High Noise Condition. Four Unit 2 Starters Replaced.Also Reportable Per Part 21
PLA-1048, Forwards Amend 44 to OL Application,Consisting of Revision 1 to Security Plan
PLA-1114, Advises That Seismic Stress Rept Will Not Be Available by 820601 as Previously Indicated.Individual Stress Repts to Be Available Between 820614-30 & Design Repts Between 820614-0708
PLA-1636, Forwards Updated Const Status Rept as of 830331 for Inclusion in NUREG-0030
PLA-2169, Forwards Updated Const Status Rept as of 840331.Info for Inclusion in NUREG-0030.Const Completed & Fuel Loading Commenced
PLA-1195, Forwards Response to IE Bulletin 81-01, Surveillance of Mechanical Snubbers. Description of pre-fuel Load Snubber Insp Program Also Encl
PLA-1054, Final Deficiency Rept Re Welding of Supports to Containment Liner Plate,Initially Reported 800416.Evaluation of 2,700 Supports Attached to Plate Resulted in 56 Fixes.Completion Expected by Fuel Load.Also Reported Per Part 21
PLA-1091, Final Deficiency Rept Re Failure of Reactor Core Isolation Cooling Turbine Exhaust Swing Check Valve,Initially Reported 810410.Valve Replaced.Discs Will Be Replaced by 820601.Also Reported Per Part 21
PLA-1073, Final Deficiency Rept Re Design of Emergency Core Cooling Pump Circuit Breakers,Initially Reported 810921.Mod to Eliminate Sneak Circuits Issued by Bechtel.Also Reportable Per Part 21
PLA-1042, Interim Deficiency Rept Re Agastat E7000 Series time-delay Relays,Initially Reported 820217.Defective Relays Identified Visually by Diaphragm colon.Fifty-two Relays Returned to Vendor for Rework.Also Reportable Per 10CFR21
PLA-1056, Final Deficiency Rept Re Separation of Macadapt Series Wpt Connectors,Initially Reported 811207.All Connectors Identified by Action Item 2 & Radiographed.Nonacceptable Connectors Replaced.Also Reported Per Part 21
PLA-1102, Interim Deficiency Rept Re Capability of Ac Electric Distribution Sys to Support Two Unit Operation,Initially Reported 820420.Design Voltage Verification Tests Conducted. Final Rept in Sept 1982.Also Reported Per Part 21
PLA-1022, Final Deficiency Rept Re Agastat General Purpose Auxiliary Control Relays,Initially Reported 811124.Relay Bases Will Be Replaced.Also Reported Per Part 21
PLA-1009, Final Deficiency Rept Re Isolation motor-generator Sets, Initially Reported on 810921.Time Delay of LPCI Underfrequency Trip Scheme Increased from 5 to 17 Seconds. Also Reported Per Part 21
PLA-1070, Responds to NRC Re Violations Noted in IE Insp Rept 50-387/82-04.Corrective Actions:Access Pit Covers Installed & Caulked.Isg & Technical Section Engineers Will Attend Training on Temporary Mod Control
PLA-1793, Final Deficiency Rept Re Pacific Valve Co Swing Check Valves.Initially Reported on 810311.Check Valves 011053 & 011054 Removed as Unnecessary.Valves 111100,111101,211100 & 211101 Replaced W/Locked Open Butterfly Valves
PLA-1000, Final Deficiency Rept Re Migration of Flaxoap Lubricant Into Electrical Equipment,Initially Reported on 810805.Possible Equipment Damage Eliminated by Reinsp & Conduit Sealing.Also Reported Per Part 21
PLA-1608, Application for License to Receive,Possess,Store,Inspect & Package for Transport Nuclear Fuel Bundle/Assemblies. Supporting Documentation Encl
PLA-1803, Final Deficiency Rept Re Miscellaneous Debris in Control Rod Drive Guide Tubes.Initially Reported on 830722.Debris Removed.Third Security Guard Posted at Reactor Vessel. Deficiency Not Reportable Per 10CFR50.55(e) or Part 21
PLA-1059, Submits Final Response to IE Bulletin 80-10, Contamination of Nonradioactive Sys & Resulting Potential for Unmonitored, Uncontrolled Release of Radioactivity to Environ. Warning Signals Installed at Demineralized Water Sys Outlets
PLA-1008, Final Deficiency Rept Re Misapplication of Marotta Excess Flow Check Valves,Initially Reported 810702.Valve Specs Inadequate Since Valves Required to Be Tested W/Water Only. Tests Indicate Minimal Nitrogen Leakage.Valves Adequate
PLA-1394, Interim Deficiency Rept Re Potential Failure of Spotmos Temp Elements.Initially Reported on 821015.Corrective Actions Will Be Completed Prior to Fuel Load.Also Reported Per Part 21
PLA-1045, Final Deficiency Rept Re Throttling Characteristics of RHR Sys Throttling Valves,Initially Reported on 811112.Present Valve Discs Will Be Replaced Prior to Fuel Loading.Also Reportable Per Part 21
PLA-1951, Forwards Updated Const Status Repts as of 830930.Info for Inclusion in NUREG-0030
PLA-1401, Forwards Updated Const Status Repts as of 820930.Info for Inclusion in NUREG-0030.Unit 1 Has Loaded Fuel & in Operations Startup Mode
PLA-1370, Final Deficiency Rept Re Failure of Contractor to Include Sufficient Margins in Initial Design Calculations to Account for Inaccuracies in Ac Electric Distribution Sys.Initially Reported on 820420.Also Reported Per Part 21
PLA-1501, Application to Amend License NPF-14,consisting of Proposed Amend 18,revising Items 2.A,2.B.(2) & 2.C.(9) Re post-fuel Loading Initial Test Program
PLA-1168, Forwards Addl Info Re Masonry Block Walls Per 820702 Telcon Request.Sink Supports Located on Wall Will Be Removed to Meet Allowable Stress Conditions.Bench Attached to Block Wall Will Be Removed from Wall Prior to Fuel Load
PLA-1139, Forwards Seismic Qualification Review Team Forms for NSSS Equipment.Remaining Review Team Forms or Justification of Interim Operations Will Be Supplied During 820628 Meeting
PLA-1166, Advises That Util Will Perform Fire Test of Tsi,Inc Fire Barrier Matl Prior to Escalation Above 5% Power
PLA-1185, Submits Results of Five Sequential Starts of Diesel Generator W/Compressors Secured,As Described in Util
PLA-1170, Requests Tech Spec Change to Carbon Dioxide Storage Tank Available Capacity for Fire Protection Applications,From 90% of Capacity to 25% of Capacity.Bechtel Ltr Re Tank Capacity Encl
PLA-1177, Discusses Diesel Generator Surveillance Requirements Resulting from 820708 meeting.As-built Installation of Diesel Generator Starting Sys Meets Design Bases Delineated in FSAR Section 9.5.6.1 & Conforms W/Srp Requirements
PLA-1030, Forwards Addl Info Re Valve Accelerations Per Seismic Qualification Review Team Audit of Util 811229 Submittal
PLA-1024, Forwards Sqrt Forms for Balance of Plant Equipment in Partial Response to Ser,Item 11
PLA-1013, Advises of Change in Position Re Branch Technical Position Cmeb 9.5-1,Position C.5.b.2(c) for Three Fire Zones.Util Intends to Enclose Minority Div Essential Raceways Located in Each Zone in Fire Barriers Having 1-h Rating
PLA-6770, Requests That Footnote 31 to Table 3.2.1 Be Revised to Read: Sys & Components So Designated Conform to Quality Group D (Augmented) Including Seismic Requirements as Defined in NRC Branch Technical Position Etsb 11-1 Parts B.4 & B.5
PLA-1074, Summarizes 820301 Meeting W/Nrc to Discuss Design Control Program for Facilities.Description of Program & Slides Presented at Meeting Encl.Independent Piping Design Review Will Be Completed About 820601
PLA-1430, Application for Amend 15 to License NPF-14,consisting of Proposed Changes to Tech Specs Re Administrative Controls, Special Test Exemption for Oxygen Concentration,Leakage in RCS & Refueling Operations
PLA-1680, Forwards Public Version of Response to Request for Addl Info Re Emergency Plan & Rev 0 to Emergency Plan Implementing Procedure EP-IP-101 Re Inventory,Insp,Operational Testing & Calibr of Emergency Equipment & Supplies
PLA-1846, Advises That Simultaneous Malfunctions of Control Sys Due to Single High Energy Line Break Bounded by FSAR Chapter 15 Analysis & within Operators & Safety Sys Abilities to Mitigate Events
PLA-1078, Forwards Documentation of GE Comments on Emergency Operating Procedures & Startup Tests & Resolutions to Comments Per NUREG-0737,Item I.C.7.Info Completes Action on SER Open Item 77
PLA-1072, Forwards Clarification of Revision 2 of Environ Qualification Rept Per 820420 Telcon
PLA-1039, Forwards Project Description for Independent Design Review of safety-related Piping Sys.Limits & Scope of Review & Means of Disseminating Basic Design Info Defined
PLA-1172, Justifies Need for Footnote Not Accessible on Tech Spec Table 3.3.7.9-1.Instruments Are Under Raised Floor & Above False Ceiling of Control Room
PLA-1182, Requests Tech Spec Section 3.11.1.1 Exemption to Delete Max Permissible Concentration for Xe-131m from Tabled Limits for Dissolved or Entrained Noble Gases.Isotope Will Not Be Significant Dose Contributor
PLA-1179, Responds to 820707 Request Re Walkdown of Masonry Walls in Control Bldg.No safety-related Items Found Attached to or in Vicinity of Subj Walls
PLA-1191, Forwards Results of Facility Entrainment Demonstration Program Developed to Meet Requirements of Special Condition C,Part C of NPDES Permit PA 0047325
PLA-1075, Revises Paragraph I.B.4 of Util Re Preservice/ Inservice Exam.Augmented Preservice & Inservice Insp Programs Have Been Established in Accordance w/NUREG-0619
PLA-1313, Forwards Susquehanna Steam Electric Station Radiological Environ Monitoring Program,1981
PLA-1540, Forwards Updated Const Status Rept as of 821231.Info for Inclusion in NUREG-0030
PLA-2189, Final Part 21 Rept Re GE Reactor Mode Switch.Initially Reported on 830407.Mode Switch Design Modified,Per Franklin Inst Research Lab Recommendations
PLA-2120, Interim Part 21/deficiency Rept Re Base Metal Cracking in Fittings Used on Class IE Electrical Raceways & HVAC Supports.Initially Reported on 840206.Final Rept Expected Prior to Initial Criticality
PLA-2075, Second Interim Deficiency Rept Re Improper Relief Valve Setting,Design Pressures & Design Temp within Several Sys. Initially Reported on 831118.Spec M-199 Revised & Code Data Repts Amended.Also Reported Per Part 21
PLA-1435, Final Deficiency Rept Re Failure to Meet Single Failure Criterion for Medium Voltage Penetration.Initially Reported on 821117.Redundant Class IE Overcurrent Protection Will Be Provided for Assemblies.Also Reported Per Part 21
PLA-1500, Suppl to Final Deficiency Rept Re Vertically Installed Anchor-Darling Check Valves.Satisfactory Testing Completed on 10 of 12 Valves
PLA-1464, Responds to IE Bulletin 82-04, Deficiencies in Primary Containment Electrical Penetration Assemblies. Bunker-Ramo Electrical Penetrations Have Not Been Used & Are Not Planned for Use in safety-related Sys
PLA-1121, Final Deficiency Rept Re Inadequate Documentation for Miscellaneous Steel,Initially Reported 810513.Discrepancies Caused by Bloomsburg Metal Co Method of Matching Mill Test Rept W/Steel to Be Shipped
PLA-1124, Final Deficiency Rept Re Vertically Installed Anchor-Darling Check Valves,Initially Reported on 820505.Hinge Arms of Check Valves 1F006 a & B Modified by Adding Right Angle Extension.Also Reportable Per Part 21